Cool Air Solutions has provided Warner Springs CA air conditioning and heating solutions since 2006. Our services include installation, repair, maintenance and more for residential and commercial clients.
Read our reviews to see why your Warner Springs CA neighbors call us first when they need help making or keeping their home comfortable.
for Warner Springs, CA
Our Reviews by City
The technicians presented an in depth analysis of possible issues and resultant issue. Very informative!
Mario - Warner Springs, CA
Great service and I trust Michael Pierson
Gudrun - Warner Springs, CA
very good service
Phet - Warner Springs, CA
Very good friendly service
Performed AC diagnostic on 1999 Goodman condenser. Upon my diagnostic client stated that the system stopped working about a week ago heâ€™s not sure if the capacitors bad. Upon my diagnostic I found multiple points of concerns that were addressed with Woody. 1. Compressor windings are no longer good and are instantly causing the breaker to trip or pop the fuses. 2. Duel secondary motor control has been blown on both fan and hermetic side terminals 3. Power disconnect was no longer sending out load to condenser. 4. Starter showed signs of painting and burn marks on contact points 5. System Contained a Phased out R22 Refrigerant As of January 1, 2020 Discuss the full condition of the system with Woody and he plans on putting the house on the martlet. We are going to give him his options whether or not he would like to replace the R22 compressor or replace the ac side of the system. Upon departure collected only diagnostic fee and supervisor will be getting back to him about replacement o
Upon arrival performed diagnostic on goodman system. System was low on charge, added 1 lb of r410a and added leak dye to system. Cooling dropped down to 52 degrees. Replaced secondary motor control that was out of range. System is operational upon departure.
Inspected upstairs cassette for operation and measured temperatures. Adjusted fan settings to circulate, recommending leaving the system set to cool at 80 so that when the loft is occupied there is not such a large demand to pull down the temperature quickly. Checked filter. Also recommending drapes or shutters for the 4 large windows to help alleviate the heat load upstairs.
Circuit board was replaced And system began heating with a 40 degree temp rise. Board is warranty for 1 year and system is fully operational upon departure
Performed AC diagnostic on 2007 Ducane Condenser. Upon my diagnostic Mario stated that just a couple months ago The heater had issues with the circuitboard and it needed to be replaced and now the AC doesnâ€™t turn on. The first place I went was to the thermostat and turned the system on to cooling and there was a tremendously long delay. Removed thermostat and jumped out cooling and everything fired up. Proceeded to the addict define that the system is a dedicated horizontal Ducane Inspected the circuitboard and found multiple burns and heat spots. Also found that the indoor blower motor was leaking significant oil from the bearing. Inspected outdoor unit and measured refrigerant pressures to find that the system has major air Restrictions. Refrigerant charge checked out although it does have a Phased out refrigerant called R22. Measured duel secondary motor control that powers compressor and fan and found that it was weak on the compressor side. High-voltage relay was also pitted on
Installed daikin 1 thermostats and translating hubs. Manually configured thermostats for operation.
18 months 0% interest or 3% cash discount
Arrived on site to perform spring tune up on a 2004 unit. Condenser located on side of home. Furnace and Evaporator coil located in attic. Washed condenser inside and out. Fan motor is leaking my oil from self wear. Primary was good and secondary is good as it was replaced last year. Unit has existing compressor booster kit. Compressor amp are high from age and wear on compressor. Fan motor is pulling high amps draws as well and why motor is leaking oil refrigerant pressure are stable and cooling home at 22 degrees. Indoor unit. Blower assembly is really dirty and with oil. Motor has been leaking oil and could fail in future. Secondary motor control is in range. Evaporator coil is dirty from lack of filter change out. Advised to stay on top of filter cause dirt could clogged up Evaporator coil and drain lines. Temperature split is good and cooling at 22 degrees. Cycled unit. Client is aware of how system is running and itâ€™s condition. Client did declined recommended work at this tim
on arrival found downflow unit running at medium speed on heat putting out a 30Â° temperature split. Switched the fan and the heat terminals so that heat is now on the low speed and fan is on medium low speed. Temperature split is now 42Â° which is warmer and still within range of the temperature split. System is working correctly at this time with a good temperature split and clients are happy with this change. Let the clients know that cooling unfortunately cannot be change from the high speed and the fan will still be loud when running the cooling. If need to change we may be able to bring the fan down to medium high but for now left the way it is.
Tested system on the heating cycle. Measured temperature rise. Recorded voltages, measured motor amp draws. Cleaned flame sensor. Tested ignitor in ohms. Tested blower motor control. Inspected duct sizes. Inspected condensate lines.
Arrived on site to perform combo tune up on a 2019 Lennox unit. Condenser outside and furnace and evaporator coil located in laundry room. Clistaed he wants unit inspected as unit is not cooling. Advised client I would be doing a full system evaluation and will not charge as I will perform tune up on unit and advised findings.founsout door unit no operational. Found its possibly over heated as client just had house painted and condenser unit was covered up. Advised big possibility since unit was covered up it over heated and shut off due to safety as Iâ€™m not seeing unit Act up at this moment. Inspected out door unit. Checked electrical compartment and components. Prism control is good. Secondary is good and in range. Fan is good and amping in range. Compressor start and run amp drawls are good and in range. Refrigerant pressure are good. And cooling. Cycled system and is operational. Inspected In door unit. Filter had a bit of over spray from paint house. Replaced filter but client
Heating system maintenance in Warner Springs
York air conditioner repair
Two system air conditioning maintenance in Warner Spings.
Performed Routine Fall Maintenance on Maytag Furnace. Checked all Electrical components and Ductwork. Reslopped drainline.