Are you having trouble keeping your Anaheim CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Anaheim CA neighbors. Call us to find out what we can do for you.
for Anaheim, CA
Our Reviews by City
Service was great. Great price for the work
Sam - Anaheim, CA
Had an issue with my air. Called cool air solutions and Luke responded. Absolutely wonderful. Fixed the issue an went over my new equipment with me til I understood.
Great Maintenance Service
David - Anaheim, CA
Very satisfactory experience. Took his time to explain and was very knowledge on the produce.
Arrived on site. Started tune up of ac system. Cleaned condenser coils, flushed out drain lines. Inspected electrical. Refrigerant charge is good. Filter is okay. Changed out blower cap under parts warranty. Unit is cooling upon departure.
Performed diagnostic on system. Unit is not cooling. Found compressor was not turning on. Found Unit completely flat on r-22 refrigerant. Went over recharge price for refrigerant. Charla decided that itâ€™s not worth fixing and they will be replacing the unit. They purchase their systems through Ferguson and have fire and ice replace it. Helped put a portable AC unit in that they had on site. System is not operational upon departure, left power to unit off.
Performed furnace tune up on a 2017 goodman. System has a 46 degree temp rise. Combustion blower and main blower motor are functioning well and amperages are in range. Hot surface ignitor is reading in range. The system has a merv cabinet with a merv 11 filter that needs to be replaced. Single secondary motor is within range however it is leaking its lubrication out of the top which is the first sign of failure. Flame sensor was cleaned and reinstalled. Duct runs are tight and free of any rips or obstruction.
Arrived on site to diagnose a 2017 Goodman system that is not cooling. Condenser located in back yard. Furnace and evaporator coil located in attic. Spoke over with client and she stated unit dose not turn on or cool. She tuned system on and was not operational. Went and inspected both indoor and out door units. Found no voltage on either units advise had to trouble shoot for power advised tenants. Checked all electrical wiring and connection were good went and checked breakers and found Furnace breaker fused tripped. Identified on breaker switches which is to furnace and Ac. Switched it back on and now had system operational and cooling. Had system run for 10 mins to ensure breaker would not trip again. Recommend adding surge protectors to unit to prevents from having shortage issues. Spring tune up Inspected indoor unit. Found few ducting used and good condition. Filter was ok as it was just replaced 3 months ago. Checked all electrical wiring, connections, circuit board, and com
Performance tuneup on the condenser
Air conditioning maintenance in Anaheim, Ca on an American Standard System.
2 system maintenance in Anahiem
Do you single system air conditioner and heater maintenance out here in Anaheim
Heating maintenance in Anaheim
Precision system tune up and electrical repair for air conditioner in Anaheim
Performed Routine Fall Maintenance on Lennox Furnace in Riverbend community.