Cool Air Solutions has provided Banning CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Banning CA area neighbors call us first when they need help making or keeping their home comfortable.
for Banning, CA
Our Reviews by City
Judy - Banning, CA 92220
Judy - Banning, CA 92220
On time , neat & thorough
Upon arrival unit was operational. Started at the furnace checked amps they were in range temp rise was in range , condensation line was clean and blower wheel was free of oil and debris. Safety switches were functioning properly. One filter was changed out of two. Upon departure unit was operational and heating.
Check System Static Pressures Check all Safety and Limit Switches Clean Condenser Coil Duct Leakage Inspection Remove Debris from the Condenser Check Refrigeration Pressures Perform Visual Inspection and Clean Service Panel Measure Starting Amperage of the Compressor Tighten Electrical Connections Measure System Amperage and Voltage Flush Condensate Drain Lines Measure Temperature Difference Vacuum Furnace Return Air Grille Clean in Place Blower Compartment Inspect Blower Wheel for Proper Balance Monitor Air Purification System Apply UV Protective Coating on Condenser Perform Energy Usage Calculation Test Condenser Pressure Switches Check Thermostat for Proper Operation / Calibration Lennox 20x25x5 Merv 11
Performed ac tune up. Cleaned outdoor coils, measured 20degree temperature split. Customer changed and provided filter. Removed debri from bottom of unit. Measured and tested capacitor. Unit is operational and cooling upon departure.
We will be moving the condenser around the corner to a new location. This price covers up to 10 ft. The move is approximately 6 feet away from the current position. Lineset and EMT will be run alongside the bottom of the wall inside the line set cover.
Arrived on site to perform fall tune up. On unit. 20 year old unit. Filter was good. Furnace is located in attic. Cycled heater and is operational. Blower ass and whee is dirty. Motor is leaking oil on borrowed time as itâ€™s working hard and needs a cleaning. Secondary control is bad and out of range and will fail if left the same. Inducer motor is operational but working hard from age. All safety switches are operational but worn out from age. Would recommend rejuvenation to unit to buy more time. Temperature rise is good. Unit is heating home good. Drain line is good at Thai time and clear. No protection on unit. Client he was okay on hearing recommendations and repairs and would just call us out of there is a issues advise I would still put recommendations in file. Client is okay and aware of condition and repairs needed to heater. Client did declined. Cycled system to ensure system operating. System is operational upon departure.
Upon arrival performed installation of merv cabinet hospital grade filtration. Sealed all penetrations, system is operational upon departure.
Upon arrival performed maintenance on 1 year old Lennox system. Checked refrigerant levels and washed outdoor coils. Coils had a lot of dirt and debree build up. Checked primary and secondary motor control. System does not have any protection from power surges. INdoor blower wheel is dirty and has a lot of build up. Circuit board and electrical connections good. Coil and ducting is in good condtion. System was reset tested and fully functional.