Heating, AC & Indoor Air Quality
Are you having trouble keeping your Lake Elsinore CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Lake Elsinore CA neighbors. Call us to find out what we can do for you.
for Lake Elsinore, CA
Our Reviews by City
Candy - Lake Elsinore, CA
The service was great. We learned a lot about our cooling system from Luis Mendez. He was extremely professional and informative.
Very polite and seems knowledgeable
Keiko - Lake Elsinore, CA
Olivia - Lake Elsinore, CA
Michael is amazing. He has very good communication skills, he is very polite, and professional. Thank you Michael for all your amazing help.
He was great.
Nicole - Lake Elsinore, CA
Ben - Lake Elsinore, CA
Michael Pierson was outstanding. Very professional. Highly recommend!
Enoel - Lake Elsinore, CA
Dwain - Lake Elsinore, CA
Supervisor Darrin was very knowledgeable about the product and and helped us to determine was packaged was best for us
Dwain - Lake Elsinore, CA
The service tech Jimmy was very helpful and explained all of our options on repairing our AC unit!
Great service and price
Fritz - Lake Elsinore, CA
Your technician Michael represents your company well. He takes great pride in his work and I appreciate that
Joe - Lake Elsinore, CA
Technician (Jimmie) On time, with details of the complete repair. Started right away with complete clean up.
Monica - Lake Elsinore, CA
Tyler is the best explained all my options for my repair and really kind
Joe - Lake Elsinore, CA
On time and informative.
Awesome service n technician
Joe - Lake Elsinore, CA
The tech was very informative n pleasant to speak with. Shared in detail the workings of my system.
Walter - Lake Elsinore, CA
David came over to set up our smart home package, friendly and professional and gave us great tips and easy way of controlling our systems. Thanks David.
Linda - Lake Elsinore, CA
Albert - Lake Elsinore, CA
David was very nice well manner and very helpful, very professional. Great job, keep up the good work..
Fernando - Lake Elsinore, CA
Marvin did a great job of explaining everything to me and made sure I understand everything. He’s great
Loren - Lake Elsinore, CA
Technician was very thorough and he inspected everything I ask Excellent job thank you
Anna - Lake Elsinore, CA
Good job in scheduling!
Great and dependable service
Jeff - Lake Elsinore, CA
Always Great Service
mpsandler - Lake Elsinore, CA
Very thorough and take good care of my HVAC system.
Barbara - Lake Elsinore, CA
Very pleasant young man, helpful and informative.
Great service for a great price
Tia - Lake Elsinore, CA
Anna - Lake Elsinore, CA
Great Customer Service
Orlando - Lake Elsinore, CA
Michael was very professional/courteous and very thorough in his work. We appreciated his service very much. Thank you!
Performed AC maintenance on 2019 carrier system. Cycled system for cooling. Checked indoor and outdoor unit electrical and system components. System is producing proper temperature split and refrigerant levels are in range. Replaced 1 inch filter. Ductwork is properly sealed and strapped. Checked outdoor unit components. Primary motor control is in good condition. Secondary motor control is within range. Pulled off condenser fan motor and thoroughly washed out condenser coil inside and out. Disconnect box does not have any fuses and is not a fused disconnect box. Also recommended adding compressor booster kit to help with compressor longevity. Homeowner wants to hold off on any repairs. Signed homeowner up on monthly ESA maintenance program and used today as AC maintenance visit. Cycled system, system is operational upon departure.
Performed AC maintenance x2 on 2 2007 units. Homeowners have not had a maintenance done to units since they moved in 4 years ago. Cycled both systems for cooling. Checked indoor and outdoor units electrical and system components. Replaced all 1 inch filters. Systems are producing proper temperature split and refrigerant levels are within range. Pulled off condenser fan motors and thoroughly washed out condenser coils inside and out. Coils were super plugged up and dirty. Performed full evaluation of system, concerns are as follows: 1. No condensation safety switches on drain lines. 2. Both Compressors are starting up loud and hard. 3. Condenser fan motors are over amping. This has caused them to work harder and also have started leaking oil, 4. Secondary motor controls on both units are out of range for compressor side. 5. Condensers were relocated and some point, and refrigerant lines were ran underneath the concrete. This could pose a problem should there ever be a refrigerant issue
Upon arrival performed maintenance. Completely opened up outdoor system and cleaned off coils inside and out. Condenserr fan motor in very good shape . Refrigerant levels good. Subcool superheat good. Temp splits good. Replaced 20x30x1 filter was replaced. Recommend to replace filter more often or upgrade filtration. Filter was completely dirty causing air restrictions. 22 degree tem split. Circuit board and electrical connections very good. Recommend adding hardstart kit to keep amperages on compressor low off start. Less wear and tear. Customer declined to do any repairs or membership. System was reset tested and fully functional upon departure
Upon arrival performed maintenance on 2016 unit. Outdoor system was completely opened up and washed out. Cleaned coil and inside of condenser caging. Amperages throughout system very good. Refrigerant levels and temp splits very good. Both filters were replaced. Circuit board and electrical connections good. Primary motor control in good condition. Secondary motor control low. Condenser fan motor good. Insulation levels in attic good. Duct work in very good condition. System was reset tested and fully functional upon departure. Please send home owner filtration and purification flyers. Please send customer CC authorization form.
Arrived on site to perform spring tune up on a 2014 system. Condenser located in back yard. Furnace and evaporator coil located in garage. Client stated the other day her system was not cooling and next day later it was so she canceled service appointment and change it to a spring tune up to see how system was running. She cycled cooling mode on. Inspected attic. Found inundated ducting used. Filter was dirty but recently changed out 2 months ago Client stated. Washed out doo unit inside and out. Cleaned, rinsed, and wiped down out door unit. Check fan blades, bearings, and motor. Fan motor is starting to leak slight oil down shaft. Checked electrical compartment and components. Primary and secondary controls are good and in range. Checked amp drawls on compressor and fan motor. Both good and in range. No protection on either units. Refrigerant pressure are good. Cycled system inspected indoor unit. Found filter dirty but client stated her husband is gunna order more and will replace t
Arrived on site to perform spring tune up on a 1993 Lennox system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues in system. Just wanted to check on air flow as to why his master isnâ€™t getting good air flow like the rest of the house. Checked and replaced filter. Inspected indoor unit and ducting and insulation. Checked electrical wiring, connections, circuit board and components. Checked blower assembly. Checked evaporator coil and drain lines. Took temperature split. Cycled system to ensure system operating. Inspected out door unit. Washed out door condenser inside and out. Checked electrical compartment and components. Check primary and secondary motor control. Checked amp drawls on compressor and fan motor. Un able to checked refrigerant pressure as service ports caps would not come off and client Said if they Arenâ€™t coming off its okay as he doesnâ€™t want them to break. The summary of findings are as followed. Condense
Cooling Maintenance: (1) Condenser fan motor is operating within manufacturer specifications (18.75). (2) Compressor is operating within manufacturer specifications (1.47). (3) The contactor is okay. (4) The battery cap is operating within manufacturer specifications at [(-1%) + (-4%)]. (5) Refrigerant levels are good. Refrigerant type is R-22. (6) The outdoor coil was cleaned. (7) The internal service compartment was cleaned. (8) Cleaned out the condensate line. (9) Found no damaged wires. (10) Tightened the wire connections. (11) The filter was replaced. Filter sizes are 18x30x1 and 20x24x1 Notes: (1) The battery cap is nearly out of range and should be replaced if it gets worse. (2) The condenser fan motor is starting to leak grease. This means the motor has overheated at least once. This part should be monitored.
Arrived on site to diagnose a 1987 system with air flow issues. Homeowners stated they will not be home and there daughter while be and spoke over with daughter as to what going on. She advised her system dose cool but there are having a air flow issues to some parts of house. Inspected indoor unit and attic. System dose operate and is cooling. Found insulation to be okay and house had insulation on attic ceiling but has fell. Found gray and black flex ducting used and in not the best conditions. Inspected all ducting and all show to have had patched up work done in past. Some ducts having kinks in it restricting air flow to rooms. Found some vents are undersized and Not enough supply to have good air flow. Found all main duct to have a fiberglass insulation box to direct air flow but is not in best condition. All ducting show to have some lose and poor connections and some not sealed properly with tape and cold temperature is being lost in attic. Found master bed rooms vents to hav
Found system non operational upon arrival. Found compressor with over 100amps of LRA. Customer approved condenser rejuvenate. Installed motor and motor controls. Also installed nest thermostat provided by customer. Cycled and tested upon departure. Customer also signed up for 1 year maintenance agreement.