Heating, AC & Indoor Air Quality
Are you having trouble keeping your Corona CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Corona CA neighbors. Call us to find out what we can do for you.
for Corona, CA
Our Reviews by City
Martin - Corona, CA
Was able to provide a great price.
Arlen - Corona, CA
Darren was knowledgeable, explained things clearly, and helped us make an informed decision on what was best for us.
Great service awesome technician
Will - Corona, CA
Jorge was outstanding in every way. Thorough in his presentation of information and options, quietly efficient and respectful in our home. Very professional and friendly. Good man!!
You guys again sent a awesome tech honest and professional thanks
Jim - Corona, CA
Lana - Corona, CA
Michael was very nice and professional. He wore boot covers in my home which was nice. He took the time to explain everything in detail so that I could understand what he was doing. We will definitely be calling back for our AC needs.
Desiree - Corona, CA
Excellent technician. Very courteous and friendly. Informative. Excellent service.
AWESOME SERVICE AND COMMITMENT
Jim - Corona, CA
From the very first time I called Cool Air Solutions over 1 year ago, I knew I had found an Air Conditioning/Heating company with a total commitment to their sales and service. From the Sales and Installation of our new system a year ago to the outstanding preventive maintenance service we received today, we know we chose the right company. We are as committed to Cool Air Solutions as they are to us. The technicians are very friendly and always explain everything in complete detail. Thanks to everyone at Cool Air Solutions
Jason - Corona, CA
Service as good as usual.
Steve Carmeli - Corona, CA
Friendly and helpful
Great and Professional service
Pedro - Corona, CA
Cool Air Solutions give for customer the best attention, my experience is wonderful, with Professional and quality solution, on concordance with the custumer nedd .
Professional, Informative & Through
Gary - Corona, CA
Looking forward to seeing the finished installation
Steve - Corona, CA
Can't say enough about how pleased I am with the service I have received
Fraser - Corona, CA
The tech was punctual, highly competent and very polite. Every employee I've dealt with in this company has been first class, Michael Pierson was no exception.
Replace both systems with listed equipment. Permits/HERS included
PTU. Found system operational upon arrival. Replaced both washable filters with new cut to fit washable filters. Old filters were clean but customer requested to replace them anyway. Customer also had some questions about air quality and running unit with doors or open windows. Customer was under the impression it was better to run the unit with the doors and windows open to bring in fresh air. Advised customer not to do that since it forces the unit to run longer and reduces the unit efficiency. Running the unit on with outdoor air coming would keep the unit running all day. Washed condenser coil. Customer stated he had just done this too a couple weeks ago. Checked electrical. Compressor is running on very high amperage. This number also goes up in higher temperatures. Customer stated that made sense since the unit doesnâ€™t work very well in high temperatures. Checked freon pressures and they are slightly low but advised customer it wasnâ€™t affecting cooling performance. He asked h
Arrived on site to diagnose a no cooling 2013 good and system. Condenser located in back yard. Furnace and evaporator coil located in attic. Spoke to client upon arrival and he stated system was working few days back and recently he noticed house was getting warm instead of cool. She stated both indoor and outdoor systems were operational. Upon arrival had client cycle cooling mode on. Found compressor was not starting up but fan would operate. Advised client I would be checking both indoor and out door units. Inspect all electrical wiring, connections, and components. Check refrigerant pressure and compressor and fan amp drawls. Advised the summary of findings are as followed. Condenser 1. 2013 goodman system. Found not operating properly upon arrival. 2. Primary start control good. 3. Secondary motor control is completely bad and not allowing compressor to turn on. Fan side was weak but able to turn on. Replaced and evaluated full system. 4. Fan is rusted up condition due to spr
Quality control check
Performed AC maintenance on one year old Lennox condensing unit
Inspected system and found extremely high static pressure(1.25â€ w.c.) due to undersized rerun and supply ducting. There is no access to get into the attic. Everything else checked out properly. Coil didnâ€™t have an emergency drain switch.
Performed AC maintenance on seven-year-old lennox condensing unit.
NO COOL. Customer said she cancelled Saturday. Said she spoke with a Travis about 20 minutes ago.
Tested system on the cooling mode and measured indoor temperatures. Inspected indoor blower and return size. Inspected coil condensate lines. Tested outdoor system supply voltages and measured motor amp draws. Tested outdoor run component and starter. Inspected disconnect fuse box. Inspected outdoor fan motor. Cleaned inside condenser and washed the coils.
Inspected the upstairs system zoning and tested for faults. Found stuck relay on the zone board feeding zone 4. Zone 1 was failing to open, power was reset and zone 1 is now open, tested multiple times, confirmed zone 4 is now closing.
Replaced Control board in Goodman furnace in Corona, recorded pressures and amp draws. Tested and verified correct operation of system.
Quality control check
Arrived on site to perforspring maintenance on a 2015 Lennox system. Condenser located in back yard p. Furnace and evaporator coil located in attic. Client concerns were with Lennox amp as it would not let them log in advise that is a manufacturer server problem thermostat is operating properly no issues at this time. Client stated Other concer was compressor made a weird noise when it operates. Advise if noise dose not appear while my maintenance I will be unable to provide a answer to noise. Client understood. Did attic and indoor unit inspection. Found black flex ducting used and insulation is good. Found filter dirty. Client supplied his own filter and replaced filter. Checked all electrical wiring, connections, circuit board, and components. all good. Blower assembly is good. Wheel is clean. Motor is good at this time. Amp drawls on blower motor are good. Evaporator coil is clean. Drain lines are good. Blew drain lines out. Tested Drain pump and is operational. Found no protectio
Performed diagnostic on 2005 systems. Owner states We have been maintaining these units and have done a good amount of work to these Units. Cycled systems for cooling. Checked outdoor unit electrical and system components. Both systems secondary motor control and primary motor control are in good condition and in range. Fan motors are both units are over amping and leaking oil. Main system fan motor is a little worse than the bedroom systems. Pulled condenser motors on both units and thoroughly washed out condenser coils inside and out. Refrigerant levels are in range. Left filters with homeowner as he preferred me not to come inside the home. Went over findings and recommendations with homeowner. Cycled system, system is fully operational upon departure.