Cool Air Solutions has provided Ladera Ranch CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Ladera Ranch CA area neighbors call us first when they need help making or keeping their home comfortable.
for Ladera Ranch, CA
Our Reviews by City
Mark - Ladera Ranch, CA 92694
Luis was professional and friendly. Would definitely welcome him back in our home.
Upon arrival, common wire was left unwired, client has issues not connecting next to wifi after he had to take off wall to charge, google has sent him different thermostats, added that common wire back for when new thermostat comes from google he can try it, but existing thermostat looks like itâ€™s charging now while on wall.
Upon arrival performed maintenance on Lennox system. Opened up system and washed out door coils. Secondary motor control is low and out of range. Client had an extra one he replaced. Advised that motor is leaking excessive oil and does not spin freely.Recommend replacing motor, client said he does not wanna do any repairs at this time. Refrigerant levels in range. Primary start is in good condition. Installed sensor predict inside and out. Verified test with Jon. System is operational upon departure.
Arrived on site to diagnose system that is not shutting off blower motor. Client stated he just had a technician come out yesterday as client got sensi predict system installed on both his units. After doing so unit will not shut off blower for downstairs system. Got in attic and found one cover off unit and client stated he had just taken off cover and didnâ€™t want to try and fix himself even though client has done reports of his units. Inspected unit and electrical compartment and connections. Found system to not be tripping any error codes. Inspected electrical wiring and found cooling wire to not be on right terminal. Wired wires back up correctly and systems was operating properly. Cycled heating and cooling to ensure system operating properly and that fan is shutting off. Recommend adding surge protectors on unit to protect for electrical surges and power outages that can damage or even short out systems and components. System is operational upon departure.
Performed tune up for both heating and cooling systems. Tested temperature splits. Recorded motor amp draws and voltages. Tested controls. Inspected ducting and connections. Inspected blower motors. Verified refrigerant charge. Checked filters. Installed Sensi predict kits for both systems.
Upon arrival performed sensi predict instal. Found secondary motor control to be out of range. Indoor blower wheel has some dust build up. Circuit board and electrical connections good. Outdoor unit is running extremely high amperages. Secondary control in range. Coils have dented fins. As I was going saftey inspection on heat exchanger, found 2 chambers to be damaged, got second opinion to make sure inspection was done correctly, advised tenant, had to shut off gas due to damaged heat exchanger. System is operational for cooling, no heat. Client is sending information over to home owner.
Upon arrival performed sensi predict install. Secondary motor control outdoor is out of range. Indoor motor leaking oil. Client has home warranties. System was installed tested and working.
Tested and maintenanced both systems. Recorded diagnostics and inspected all components. Tested ignitors and battery capacitors. Measured voltages for both indoor and outdoor equipment. Cleaned condenser coils and verified refrigerant charge.