Are you having trouble keeping your Chino CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Chino CA neighbors. Call us to find out what we can do for you.
for Chino, CA
Our Reviews by City
Ritesh - Chino, CA 91710
Luis was great! He was very thorough. I am very happy with his services!
Great service. Great price very nice guy.
Darren - Chino, CA 91710
Very nice experience. No pressure great guy.
Duct job completed, airflow properly balanced with dampers
Arrived on site to diagnose a no heating 2006 carrier unit. Spoke to husband and they stated they had another company servicing unit but are no longer using them. Bill stated he had us out in summer and got repairs done then but had never tested to run the heater as it was in summer and now that they tried to fire up unit heater did nothing. Arrived and cycled heater and thermostat clicked but nothing happened. Checked electrical compartment and wiring. Found power but there was not sending the calling command and tires to jump unit at the board and u it did not operate. Found board doing a lot of clicking but not turning on unit. Wires are good and found thermostat bad. Cycled at board it self and unit staters clicking but not turning it on. Advised client of issues going on. They are aware unit is old. Blower motor is leaking a lot of oil and covered in dirt build up. Found burn marks on board from operation and age. Called up Lynn and went over all findings and areas of concerns. Ly
Performed a heating maintenance on a 2016 Goodman system. Cleaned and Adjust Burners. Check Combustion Air for Proper Venting. Examine the Heat Exchanger for Damage / Corrosion. Test Furnace Safety Controls. Inspect Gas Piping. Tighten Electrical Connections. Measure the Voltage and Amperage. Flush the Condensate Drains. Measure Tempurature Difference between Supply and Return Air. Vacuum Furnace Return Grille. Adjust Gas Pressure & Pilot. Clean in-place Blower Compartment. Inspect Blower Wheel for Proper Balance. Check the System's Static Pressures to Ensure Proper Airflow. Inspect Duct Connections for Air Leaks / Sizing / Insulation. Check all System Safety and Limit Switches. Clean Flame Sensor. Inspect Carbon Monoxide Detector. Check Thermostat for Proper Operation / Calibration. Filter was changed out. System was fully operational at time of departure.
Arrived on site to install parts
Upon arrival client said a company did drain line repairs and it didnâ€™t fix the issue. Inspection found the primary pan of the evaporator coil had cracked. Also found evaporator coil leaking refrigerant. Found issues with the condenser. Condenser fan motor is leaking oil and over amping. Capacitor is also low. Need to replace those as well. Advised client of issues and they moved forward with the install. Advised client to not use system until its repaired on Monday.
Client stated no cooling -System was not operational upon arrival -Fan motor and secondary motor control needed to be replaced -The starter was also in rough condition -Fan motor, smc, and start were all replaced -Condenser has a full electrical rebuild -System is operating properly, motors are not drawing too much power -Refrigerant levels are within range -Client is aware these repairs are not going to make the system bulletproof -System is cooling
Upon arrival performed maintenance on cooling system. Outdoor system opened up and cleaned entirely. Secondary motor control is in range. Hardstart on compressor is beginning to climb due to age. Primary starter has small pitting where contacts meet. Performed blower wheel cleaning. Advised moving over to upgraded filtration will Benefit system by keeping it as clean as possible. Ducting is in good condition. Put system back together. System is operational upon completion.
Upon arrival performed replacement of high limit switch. System is operational upon departure.
Upon arrival performed heating tuneup. Indoor motor is good and in range. Borrower is beginning to get dust buildup. Circuitboard and electrical connections are good. Amperages through our system or in range and efficient. Wiped and wax entire furnace cabinet. Damaged switch and blower will orderFrom Goodman tomorrow morning client would like to visit next week because he is only available next week. Static pressures throughout system are in very good condition. Ducting is nice and strapped. Gas valve in working order flame sensor cleaned. System reset tested and fully functional for departure.
Thermostat was blank. Ceiling saver switch was tripped and inoperable causing a block in the low voltage circuit. Installed new safety switch and cycled system.
Goodman Ac maintenance in Chino Hills, Ca.
Performed routine spring maintenance on trane unit. Installed safety switch
Furnace maintenance in Chino
Doing a single system air conditioner maintenance out here in Chino
HA estimate A/C system