Air Conditioning, Furnace, Indoor Air Quality in San Bernardino CA
Are you having trouble keeping your San Bernardino CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your San Bernardino CA neighbors. Call us to find out what we can do for you.
for San Bernardino, CA
Our Reviews by City
Great Customer Service!
Rhonda - San Bernardino, CA 92407
Thank you Michael for a job well done!
Rhonda - San Bernardino, CA
Michael, our technician, is a very pleasant young man...he is also knows and does his job well and is very professional. The office reps at Cool Air Solutions are always so kind and professional. It's been a pleasure working with a local company that has provided excellent service!
Excellent attitude and service
Teresa - San Bernardino, CA 92404
The price was as promised and the future repairs suggested were given with a price. No arm twisting but a good summary of why the repairs are needed.
Pam - San Bernardino, CA 92407
Polite, on time and did a very efficient job. Thank you
Performed AC diagnostic on 20-year-old Package unit. Upon my diagnostic I found that the system was not powered although 240 V was present. Upon further inspection found that the circuit board had multiple burns front and back of the board And was supplying 24 V intermittently. Once contactor pulled in compressor and fan will turn on although compressor will go on to thermal overload due to windings overheating. Was not able to check refrigerant pressures the customer stated that he had an HVAC technician friend come over and tell him that there is Solder points that are cracked which could entail and leak cannot be for sure until system is fully operational and pressures are able to be checked. Recommended replacing circuitboard first and starting there and seeing what comes next this can be a costly process.
Upon arrival performed diagnostic. No voltage to outdoor system. Installer coming out to re run thermostat wire. Office will follow up with Alvaro to schedule appointment.
furnace maintenance in San Bernardino in San Bernardino
Heating maintenance in San Bernardino
Air conditioner tune up
Air conditioning troubleshoot and repair in San Bernardino
Radio Promotion AC tune up
Air conditioner maintenance in San Bernardino.
Package maintenance in San Bernardino
Performed total system rejuvenation on lennox system.
Performing a total system maintenance on Goodman, Ducane and Armstrong Aire equipment for a first time client in Devore
Two system rejuvenation
Performed full system rejuvenation on carrier system.