Heating, AC & Indoor Air Quality
Are you having trouble keeping your Menifee CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Menifee CA neighbors. Call us to find out what we can do for you.
for Menifee, CA
Our Reviews by City
Great service knowledgeable friendly conside
Diane - Menifee, CA
Jimmy was respectful of my home. Wore shoe slippers and a mask. Very professional and responsible young man. He gave me options in regards to my a/c and recommended clean air purifier
Alicia - Menifee, CA
Had the best experience with Cool Air Solutions. Called for help with our AC and Luis came out same day and helped us determine what needed to be done. And Darren came out the very next day to go over our options with us. Can’t wait for our new system to be installed. Very satisfied with the customer service!!!
Daniel - Menifee, CA
Excellent job. Very informative. Thank you.
Joseph - Menifee, CA
Reliably good service
Mark & Leslie - Menifee, CA
Cool Air Solutions installed our HVAC systems a few years back and has maintained it ever since. The system drastically changed the comfort level of our home and our lives for the better. The company has a top-notch quality culture. Justin knows his stuff. We recommend both Cool Air Solutions to anyone in the Menifee area looking to upgrade or repair their air conditioning system.
Prompt service, good prices
Anthony - Menifee, CA
Prompt service, good prices, flexible payment options.
Rosa - Menifee, CA
Dan - Menifee, CA
Mike came out to give me an estimate on AC service. He was very thorough and accommodating. What sets him apart from most of my experiences is how friendly and easygoing he is. I’m looking forward to working with this company.
Judy - Menifee, CA
Michael did a yearly service of our system. He was very professional and courteous while in our home. He fully explained what the service entailed and explained the actual costs. He also explained the service contract.
George Cervantes was a very cordial and knowledgeable with his service. Everyone should be able to have such a wonderful experience. He was beyond pro
Monica - Menifee, CA
My experience was awesome. Great customer service . Kinberly was very helpful and George Cervantes exceptional !
James - Menifee, CA
Tyler arrived on time and was very professional, knowledgeable on his products. Completed the cooling system tuneup in minimal time which allowed him to ask me if I had any questions or concerns regarding my system. I will definitely recommend to my neighbors and friends.
Super happy with service and much cooler!
Randy - Menifee, CA
Great service! Very friendly and saved us a lot compared to other company we called first!
Carlos - Menifee, CA
Mr Torres was very professional and very polite.
Dora - Menifee, CA
Kevin - Menifee, CA
Initially thought it was going to be a maintenance visit, but had to call for an earlier visit to run diagnostics due to lack of cold air coming out. They fit me in the next day (over a week ahead of my initial appointment) and were able to take care of all the issues my unit had. Technician was friend, honest, and upfront about everything. Answered all the questions I had as well. Overall, very satisfied with the service we received!
Beyond the call of duty
Alexander - Menifee, CA
Nichole and Brian went way beyond what is normally expected for customer service. After hours on Friday, my air conditioning system shut down (a 95+ degree day). A call to CAS was answered by Nichole. I explained the situation to her and she found where Brian was, contacted him, and had him contact me. Brian called me after 7pm and guided me thru the procedure of re-setting the water sensor switch. Air came back on. PS. Had CAS back on Monday to replace the bad sensor. I'm a happy camper!!!
good customer service
John - Menifee, CA
Still waiting for my invoice and service contract !
Danielle - Menifee, CA
Jason was very professional. He was straight and to the point on what needed to be fixed and what our options were. He was very respectful and worked in a timely manner to get the job done. When it is time for us to get a whole new unit we will definitely be calling the company back
Great Service, Very Polite, Honest, Covers everything detail and/or question
Deborah - Menifee, CA
Sandra - Menifee, CA
Steve - Menifee, CA
Brian was very helpful and explained everything in detail. Excellent service.
Mike - Menifee, CA
Great service very professional
Mike - Menifee, CA
Great service and very professional
Maureen - Menifee, CA
Very professional and helpful.
service was great
Carbon - Menifee, CA
Upon arrival performed maintenance. Outdoor condenser fan motor in good condition. Amperages throughtout system very good. Refrigerant levels very good. Had some insulation left over in van and re wrapped customer line set, as dogs chewed it up. System was completely opened up and washed inside and out of coils and inside caging. Replaced 2 20x30 filters. System is operational upon departure.
Also includes re insulating linset at ac and coil. This will be an el16 instead of a an ml14
Performed diagnostic on 2012 Carrier system. Homeowner stated that system is not cooling. It blows air but it is not cold. Cycled system for cooling. Indoor unit kicks on. Outdoor condenser fan motor is kicking on, but compressor is unresponsive. Checked unit electrical and system components. System is recieving low voltage command as well as high voltage, but compressor is not kicking on. Found a bad secondary motor control on compressor side. Also found a very burned and pitted primary motor control. This system is a single stage unit zoned off into two zones, which is not properly designed and should not be set up in this manner as this causes excess wear and tear on unit. Recommended adding compressor start kit to unit as it kicks on more times in a day than a normal unit would and to prevent some stress on compressor start up. Went over findings and recommendations with homeowners daughter. With homeowner approval, went ahead and replaced primary and secondary motor controls. Cycl
system not cooling. Condenser not coming on.
Performed diagnostic on 2007 Goodman system. Homeowner states system is not cooling. Said they heard a loud bang and it stopped working ever since, hasnâ€™t been working in over a month. Cycled system for cooling. Indoor unit kicks on and is blowing air. Outdoor unit is kicking on, but only the condenser fan motor. Compressor is unresponsive. Checked system electrical and components. Found a bad secondary motor control which was not allowing the compressor to kick on. Primary motor control also has some pretty bad burning and pitting at contact points. Put in a temporary secondary motor control and tested system. Compressor and condenser fan motor are operating within range. System is operating on r-22 refrigerant, which has been phased out at the beginning of this year and is more expensive. Went over findings and and recommendations with homeowner. He approved to go ahead and repair the primary and secondary motor control. Replaced primary and secondary motor controls. Cycled system
Found system non operational upon arrival. Customer stated unit was blowing warm air. Upon inspection found both fuses blown. Checked circuit breaker and tried to reset it. Breaker would not reset and is stuck. Customer stated he had heard the compressor making loud noises in the last couple of days. Checked compressor windings and did find the compressor shorted or grounded. Winding resistance was weak for start winding. Capacitor was reading well within range. Gave customer some options on repairs but I do not recommend them due the condition of the equipment. Customer went over replacement options with comfort advisor. They are thinking it over night and will contact comfort advisor in the morning. Unit non operational upon departure.
Performed AC maintenance on seven-year-old Trane condensing unit. Paul my maintenance there were a few points and concerns that were addressed 3.5 ton Trane- 1. Found that systems refrigerant charge was very low added in about 2 pounds 2. Recommended putting in leak dye To pinpoint location of refrigerant leak 3. If system becomes low again on 410 a charge leak dye must be added.
Performed AC maintenance on 12-year-old Goodman condensing unit. Upon my maintenance I came across a few points and concerns that were addressed. 5 ton GOODMAN- 1. Found that 410 a refrigerant charge appears to be overcharged causing high pressure to shoot above rated psi. 2. System may also contain restriction in TXV if system has refrigerant recovered out and pressures remain the same. 3. Found that condenser fan motor was completely rusted in over amp in at 1.5 4. Compressor also pulling extremely high amps from what it is rated it may cause compressor use much more energy and put it in a higher risk of failing. 5. Compressor pulled about 118 A on lock rotor start up this is a very hard start up and recommend that a compressor saver kit is added to reduce the start up amperage. 6. Static pressure on indoor ductwork and system showing a total of 0.83 which is very high this is due to an undersized return vent. 7. Starter on system which axis breaks showing signs of pitting on contact
Unlit youâ€™re control check
Repaired pinhole leak at the