Are you having trouble keeping your Rancho Santa Margarita CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been solving these problems since 2006 as we repair, replace and maintain the heating and cooling systems of your Rancho Santa Margarita CA neighbors. Call us to find out what we can do for you!
for Rancho Santa Margarita, CA
Our Reviews by City
Maria - Rancho Santa Margarita, CA
Great service and thank you for explaining everything to us.
Great service, straight up guy, very clear on what is planned
Kevin - Rancho Santa Margarita, CA
Brian did a great job of going over the plan and offering the best value project for my budget and goals.
Performed diagnostic on 1995 hydronic system. Homeowner is dissatisfied with the noise the system produces while running the unit. Noise is due to design of system . Grill on door is undersized creating poor airflow. Added seal on door panel to reduce noise. Inspected outdoor unit. Refrigerant levels are ok. Coils are deteriorating. Compressor is having trouble starting. Condition was discussed with the homeowner. They want to go over system options with a supervisor. Darren is scheduled to return.
Performed maintenance on a 1996 Lennox gas furnace. Customer reports unbalanced airflow through the house. Frequent use of heater this season. System kicked on ok. The heating temperature split is very high at 71 degrees. This is a cause for concern with a system this age. Sensors and switches were cleaned and tested. Static pressure is high. Combustion blower is in ranges battery cap is ok at this time. Primary blower motor is heavily leaking oil and leaking oil because the Blower wheel is very dirty and rusty. This should be replaced if any number of years is expected moving forward. A safety check was performed with permission. I found the heat exchanger to be very hot, many hot spots and weak spots in numerous areas. This condition was discussed with the homeowner. They want to receive a equipment appointment. System is operational at end of appointment.
Arrived on site to perform spring tune up on a 1996 lennox unit. Condenser located in back yard. Furnace and Evaporator coil located in attic. Client state upstairs isnâ€™t getting as good airflow as down stairs. Washed condenser inside and out. Unit really dirty. Primary is burnt up and should be replaced. Secondary motor control is good but is boarder line almost out of range on compressor side. Fan motor is bad and over amping and advised could fail at any time. Compressor start up are high but in range. Run amps are almost at max amps pulling 24 and max rated at 26.9. Advised compressor is on borrowed time and could fail due to age and working hard. Pressure are good and cooling home at 20 degrees. Filter were dirty and replaced. Blower blower unable to access and could be dirty due to filters dirty. Motor pulling high amps. Evaporator coil is dirty and debris. Drain lines due have dust and debris and no overflow safety switches. Overall found system is restricted of airflow and i
Tested heating gas pressure. Removed the second stage from the thermostat settings. Found disconnected supply duct supplying the upstairs bedroom and bathroom near the thermostat. Found and removed large blockage in the master bedroom supply grille. Cleaned the filter.
Collected a $600 deposit. Balance due will be 5501
Performed Furnace diagnostic on 1990 Rheem system. Upon my diagnostic system was experiencing intermittent behavior. 1. Found that circuitboard had Multiple burns and heat marks this could be an indication of a faulty board although cannot confirm it until new board is installed 2. Indoor blower motor has leaking oil from bearing and is over amp due to this, This can lead to the motor either locking up or overheating 3. Secondary motor control is becoming weak due to high amperage of fan 4. Condensate line are plumbed in correctly with the wrong material. 5. Duct work is not sealed correctly, This can cause lower Airflow and air Leakage 6. Static pressure was 0.90, Static pressure is the airflow of the system due to this being so high this Can cause complications with the heat exchanger overheating and Began to form cracks Recommendations- 1. After market Circuit board Is installed to solve intermittent behavior issue 2. Indoor blower motor is replaced due to oil leakage in high ampe
A.c. maintenance in Santa Margarita