Heating, AC & Indoor Air Quality
Cool Air Solutions has provided Murrieta CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Murrieta CA call us first when they need help making or keeping thier home comfortable.
for Murrieta, CA
Our Reviews by City
Great Service and Very Knowledgable Technician
Alex - Murrieta, CA
Michael is very good at his craft and we will gladly bring our business back with cool air solution. He was both knowledgeable and informative with us regarding our units. Thank you Michael for your service.
Patrick - Murrieta, CA
Luis Mendez very professional.
Blessing - Murrieta, CA
Kristen - Murrieta, CA
Provided great detailed information about our units . Pleasure to work with
Technology, can’t live without it but it can be a pain in the !!!
David - Murrieta, CA
After 2+ years of working my Honeywell thermostat stopped connecting to my WiFi making my phone app not useful. Luis, my Cool Air tech has been out to the house trouble shooting the issue twice (even putting a new thermostat in) but to no avail. He and Cool Air have done everything they could and are still trying to figure out the issue. They are suggesting I go to the Nest thermostat (which is what I will more then likely do. Anyway, I recommend Cool Air (been using them for 5+ years) as they and their technicians are helpful and professional.
Keeps my heat and cool running
Kimberly - Murrieta, CA
Cool Air maintenance plan has kept my home cool in the summer and warm in the winter and prolonged the life of my units. Very happy.
Jarvis is absolutely great
Linda - Murrieta, CA
Javier - Murrieta, CA
I learned a few things about my A/C The technician was very knowledgeable and clear explaining everything
Micheal - Murrieta, CA
Jimmy is a Great Asset to your company! He explained everything fully and then some. He went above and beyond to not only answer my questions and make sure I knew how to do the things I asked him about.
Chris Williams - Murrieta, CA
We like being a customer of Cool Air Solution for the last 10 plus years
John - Murrieta, CA
Chris - Murrieta, CA
Tyler was awesome, was super upfront before starting the work and was very knowledgeable. Thank you for putting up with our million questions:-)
Great AC Service!
Brett - Murrieta, CA
Luke was on time, professional, and very easy to work with. I was very happy with my service.
Joe - Murrieta, CA
Michael is an excellent representative for Cool Air Solutions
Judy - Murrieta, CA
Cool Air is a wonderful, dependable company who goes way above and beyond for their customers, every step of the way....
Answered all my questions
Clayton - Murrieta, CA
Very patient and knowledgeable. Quick and efficient.
Mary - Murrieta, CA
Always very professional service from Cool Air Solutions personnel. My system is 3 years old and with annual inspections have not had any problems. Professional installation and excellent maintenance.
Great service with quick appointment.
Enrique - Murrieta, CA
Awesome service. Detected problem quickly. Got an appointment in less than 24 hours in summer!
Maintenance - Murrieta, CA
Brain was on time, courteous and informative. Also, the office staff did an excellent job tracking me down to confirm the appointment.
Carol - Murrieta, CA
The tech was very professional, neat, efficient, and personable.
the tech was very professional and very friendly. He explained to every question I asked.
William - Murrieta, CA
I am definitely planning to use Cool Air Solutions for my winter furnace check and maintenance.
Great company. Great Tech
MDIMAGINATION - Murrieta, CA
Cool Air Solutions and their Tech Michael Pierson are trusted advisors. I can always count on Michael P. and Team to be prompt, give me a 15 minute window confirming their on time arrival, and exceed my satisfaction. The office staff is equally friendly and accommodating to any request. Great company to work with.
Jeff - Murrieta, CA
Micheal - Murrieta, CA
Luke did a great job
Brian was great
Keith - Murrieta, CA
Performance tune up for both heating systems
Inside of air handler cabinet Dust and debris has built up on scroll wheel and walls. This is due to the washable filter on the downstairs return washable filters only filter out about 10% of those particles. Downstairs system (TRANE) 1. Air scrubber plus ionizes entire house along with disinfecting all surfaces with hydrogen peroxide in airstream. Reduces all dust buildup 2. 5 inch thick Merv 11 cabinet To stop 90% of dust particles on high efficiency filter (6-12 month lifespan of filter) 3. Blower wheel cleaning by removing indoor blowerâ€™s and spraying down scroll wheel outside with Safe chemical cleaner.
Client under assumption appointment was tomorrow. Let office know.
Installed nest thermostat in the front office
Customer did not want Furnace maintenance, only AC. Performed AC maint on 2010 system. Cycled system for cooling. Checked outdoor unit electrical and system components. Amp draws are within range. System has really bad wiring with added secondary motor controls. Homeowner believes that was done by previous homeowners. Pulled condenser fan motor to thoroughly wash out condenser coil. Refrigerant levels in range and system is producing good temperature split. Checked indoor unit electrical and system components. Replaced 1 inch filter which was extremely dirty, has not been changed out in over a year. Went over findings and recommendations. Cycled system, system is fully operational upon departure.
Control board burn out
Quality control check
Returned to perform repair and replace filters. Replaced hot surface ignitor. Cycled system, system is now fully operational and is heating properly. Replaced all 1 inch filters. Work is complete.
Performed AC maintenance on 2 systems.1 system is a 2005 second system is a 2012. Cycled systems for cooling. Checked outdoor unit electrical and system components. Amp draws on upstairs unit which is the older of the two are fairly high. Condenser fan motor is starting to leak oil. Secondary motor control and primary motor control are both within Range. Hard start kit also within Range. Downstairs system amp draws are high and loud on start up. System is not equipped with compressor saver kit. Pulled condenser fan motors and thoroughly washed out condenser coils. Checked indoor units electrical and system components. Both indoor blower motors are starting to leak oil. Temperature splits are in range. Cycled systems, systems are operational upon departure. Turned system over for Replacement Options. Homeowners interested in possible system replacement with zoning. Field Supervisor Darren will be coming out on Monday April 30th from 12-2.
Sent work order through email. I did not go to the property
Replace furnace with new Lennox furnace, increase exhaust vent size to 4â€ adapt to and seal all ducting. Replace thermostat. Includes permits/HERS testing. Patch Attic Access. Convert Furnace to Propane.
Performance tune up for both heating systems
Performed AC MAINT on 2 15+ systems. Cycled for cooling. Checked outdoor units electrical and system components. Started with Loft system. Amp draws on fan motor and compressor are high, but still within allowed range. Secondary motor control is in range. Primary motor control has slight pitting. Refrigerant levels are low for this unit. System is only producing a 12 degree temperature split. Checked main system electrical and system components. Amp draws on condenser fan motor are above rated amps. Amp draws on compressor are also very close to over amping. Primary motor control has burning and Pitting on contact points. Refrigerant levels are within range and system is producing proper temperatures. Performed outdoor coil wash on system. Went over findings and recommendations with homeowner. Homeowner is looking to replace over repair. Set up turnover for Darren to come out a Monday March 23 from 2-4pm to go over replacement options. Homeowners are interested in full system with
Upon arrival performed maintenance on 2 duct electrical units. Indoor motors are both leaking oil. Blower wheels are dirty. Outdoor condensers were washed and cleaned. Primary power distributor is pitted and burned. Secondary motor control is out of range. Hardstart kits are recommended on older piece of equipment to help compressor kick on. Refrigerant levels good. System was reset tested and fully functional upon departure.
Installation will be Wednesday 3/17/20
Quality control. Check
Replaced Merv Filter. Explained and recommended performing routine maintenance on equipment. No other work performed.
Phone estimate only
Day 2 of install
25,600 due upon completion. Total after all rebates $23,800
Performed diagnostic. Homeowner states furnace is not operating. He has not kicked it on since we were last out to do work last month. Cycled furnace for heat. Furnace is Unresponsive. Found door to furnace not shut correctly which was not pushing door switch In to give power to unit. Secured door correctly. System kicked on and started heating. System is fully operational upon departure. No charge, this is a callback on previous work.
Upon arrival performed maintenance. Indoor blower motor is leaking oil & is running really hard. Not replacing motor can cause serious issues with air flow, seizing up, no hot air or cold air. Blower wheel is dirty and needs cleanings. Evap coil is gathering dust build up. Inducer motor is close to max amps. Safety switches are good. Heat exchanger has a lot of heat marks, did not identify crack. System was reset tested and fully functional upon departure.