Cool Air Solutions has provided Hemet CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Hemet CA area neighbors call us first when they need help making or keeping their home comfortable.
for Hemet, CA
Our Reviews by City
Paola - Hemet, CA
Mike - Hemet, CA
Jimmy nice guy got the job done im happy
John - Hemet, CA
He was very good and answered all the questions I had
Darrel - Hemet, CA
Service was great
Helene - Hemet, CA
Helene - Hemet, CA
Great knowledge on technician part.
Yvette - Hemet, CA
Evelyn - Hemet, CA
He did a good job thx u
Great and professional service highly recommend
Jheovany - Hemet, CA
Diane - Hemet, CA
Very nice, professional and personable
Howard - Hemet, CA
Technician, Jimmy, was most helpful. Very professional as he went through the service steps then met with me to go over findings and observations. Appreciated his knowledge and advice.
Troy - Hemet, CA
Nice service man, he was able to fix all our problems with the AC.
Diane - Hemet, CA
On time. Polite and knowledgeable
Christine - Hemet, CA
Very helpful. Explained what he was doing.
Every year totally honest & professionak
Jerry - Hemet, CA
Used 4 yrs since bought......very Honest...//////
Every year totally honest & professionak
Jerry - Hemet, CA
Luke as become part of our family when we need service on items. Always explains well & cleans up everything.....Outstanding in all ares of communication & service...
Dawna - Hemet, CA
Travis was an excellent service tech. Perfect representative to enter a customer's home. Clean, well groomed and very personable. Performed his tasks and took time to explain the needs of my HVAC system without a hard sell. Highly recommend Cool Air.
5 STAR ALL THE WAY!!
Terry - Hemet, CA
Good callback and appt. setup procedures. Mike called to confirm he was on the way and arrived on time. Pleasant personality and explained what he was doing and what my system needed. Very happy from start to finish. I will definitely recommend CoolAirSolutions! and use them again.
Cindy - Hemet, CA
Alway's great, reliable and professional customer service!
OUTSTANDING FIVE STAR
Gerald Clark (Jerry) - Hemet, CA
Luke knew is business.... When opened found 2 brass cover nuts not put back by last June by man that new nothing and had to call into find out about location of above outlets.... Luke did a great job of checking and explaining to me... Also was very good....
Performed Fau maint on 2016 Lennox System. Cycled system for heat. Checked electrical and system components. Temperature split between supply and return is in range. Blower wheel and evaporator coil is within range. Replaced filter with filter provided by homeowner. Brushed off any dust that was inside of the filter cabinet. Homeowner stated that she noticed more dust than usual. Recommended adding a whole home air purification system to help with the dust inside the home .Cycled system, system is fully operational upon departure.
Performs follow up for client as to see if other company took care of repairs for client or if she was still interested in replacing. Client stated they have yet to come out and diagnose unit. They would be coming out today 10/18 from 11-1. She said she would then find out and see whatâ€™s is going on and what she would do frond there. Advised would follow up at the end of the day. Clips aware and will let us know then.
Arrived on site to perform AC maintenance on 2 12 year old Aireflo units. Cycled systems for cooling. Checked outdoor unit electrical and system components. Outdoor condensers have basically been completely rebuilt and all components are still in order and within range. Systems are pulling amperages on the inefficient side but still cooling. Ran systems through inspection checklist. Pulled condenser motors off and thoroughly washed out condenser coils inside and out. Checked indoor units electrical and components. Temperature splits are within range. Homeowner will be replacing his filters as they were pretty hammered. Went over findings and recommendations. Cycled systems, systems are operational upon departure.
Arrived on site to diagnose down flow unit not lighting up for heat. Client had full system replaced by synergy she stated. Upon arrival she said the pilot would not she stated it just needed to be lit up. Advised her I would need to look first to be able to diagnose unit. Unit fan would also not shut off. Client would shut off main 120v the the light switch that was in closet to shut unit off as fan would run non stop. Advised her thatâ€™s not good and showed her the right switch to use to shut off unit. So found that unit was not operational or operating properly so client is aware of before we start to diagnose unit. Client is aware. Advised thesummary of findings are as followed 1. 2017 Down flow unit 2. Found low voltage was not at thermostat and it was powered up only cause it has batteries. 3. Inspected electrical compartment. Found 120. Live and at transformer and to board. Found low 24 voltage being sent to the board. Board was not sending it out to terminals to thermostat.
Arrived on site to diagnose no heating unit. Upon arrival found unit not turning on in heat and would not light. Advised could be board just failing and client wanted to replace board. Replaced and cycled heater and is now operating and operational upon departure. Client is happy with repair and todayâ€™s visit as unit is now heating home up. Recommend adding surge protectors in future
Tech arrived on site. Breaker to condenser had tripped. Client said fan motor wasnâ€™t spinning. Checked compressor and it was not grounded. Testing found that fan motor had failed. Installed new fan motor and compressor savor kit. Compressor run amps are high. Fan motor amps are good. Due to age and condition of unit, itâ€™s recommended to budget for replacement of AC system.
Arrived on site to perform fall tune up on Downflow 2014 unit. Client stated no issues. Cons located in back yard and furnace itâ€™s located in a laundry room closet. Cycled heater and was good.motor was replaced no protection on unit. Filters were dirty and replaced. Client keeps them on hand. Blower assembly is dirty but okay just want to keep dirt out from entering unit. Found control board burnt up on relays. Advised no good and board is still operating but could fail in future due to bad condition. Showed client and she saw and is aware of condition. Client is aware of how unit is running and conditions. Cycled system to ensure system operating. System is operational upon departure.
Arrived on site to perform diagnostic on 16 year old system. Homeowner states that system is not cooling. The indoor unit is blowing air, but outdoor unit fan is not spinning. Cycled system for cooling. Outdoor unit compressor turns on, but fan motor is not turning over. Checked system electrical components and found a dead secondary motor control. Spun fan manually to get it turned on and check the amp draws and refrigerant pressures. Amp draws on condenser fan motor are above rated maximum, and motor does have oil stains throughout which is causing the motor to work harder and drain the secondary motor control. Went over full findings and recommendations with homeowner. Homeowners are only at this home for a couple months out of the year, so they decided to move forward with repairs for now. Went ahead and replaced secondary motor control as well as condenser fan motor. Signed homeowners up on yearly ESA maintenance program. Cycled System, system is fully operational upon departure.
Tech arrived on site. Found the condenser non operational. Inspection found the capacitor had been miss wired. Tested the capacitor and it is good. Re wired the capacitor. Tested operations. Unit is 25 years old. Pulling high amperage. Motor is rusty. But itâ€™s operational. Client signed up for monthly maintenance plan. Unit is operational upon departure.
6-24 months 0% interest available
Tech arrived on site. No airflow throughout the house. Got attic access and found the motor controller had failed. Installed new motor controller to test motor. The motor is operational. Found the return duct to have collapsed internally from unknown causes. Was able to force the duct open. Unit is getting better airflow now. Also found burn marks on control board. The board might fail soon. Itâ€™s still operational now. Tested outdoor start components. Found the dual secondary motor controller to be weak but within range. Compressor drawing high amps. Recommend budgeting for replacement soon. Client signed up on maintenance program. Did first visit tune up while on site. Unit is operational upon departure.
Upon arrival performed diagnostic, client just wanted to check system make sure itâ€™s not going bad. Found condenser fan motor to be running at max Amps. Secondary motor control is in range. Primary starter is pitted and burned at contacts. Return is very dirty with dog hair. Blower wheel is extremely dirty. Secondary control in range. Filter was clean. Client declined any repairs, says it is to expensive, she is a 93 year old, and would like to just leave system the way it is. Signed client up for membership. Please send paper copy as client has no email.
Upon arrival performed diagnostic, found system to be non operational for compressor. System was not kicking on. Found system to have a dead battery, replaced and got system up and going. Check pressures and levels to make sure system is good, found refrigerant levels in range. Client had 5 registers closed with dirty filters. Advised we have to leave them open at all times. System is operational, client declined maintenance program at this timez
Upon arrival performed installation of filter drier, and TXV. System was vacuumed down to 538 microns, vacuum held to 700 after turning off. Pressurized system to 400 psi. System held no leaks. Charged system up, system is now cooling with an 10 degree subcool. System is operational upon departure.
Upon arrival performed diagnostic and found system to be jumping up and down on refrigerant cycle, client stated coil gets frozen up. Home warranty installed system. Advised client? Client is fully aware. System is operational but has issues in refrigerant cycle .
Upon arrival performed diagnostic. Found system to be no. Operational with the fan spinning back wards. Client decided she does not wanna mess around with it, would just like to replace. Installing new system Monday morning. System is non operational .
Arrived on site to perform spring tune up on a 2013 lennox unit. Client stated no issues. Condenser located in back yard. Furnace located in garage. Washed condenser inside and out. Checked electrical compartment and components. Found primary starter worn out on pittings. Secondary motor control was out of range and bad. Recommend replacing both components. Fan motor was over amping from 1.4 max rated at 1.0. Advised due to age and operation of system. Advised in future could fail but is still operating. Start up amp on compressor weâ€™re in range just high. Recommend adding a compressor booster kit to help prevent hard start up and prolong life of compressor. Run amps are good and in range. Checked pressure and are good and cooling home at 22 degrees. Filter was replaced as she dose supply her own filter. Unit is a bit dusty recommend stay on top of filter as itâ€™s entering unit. No protection on unit. Recommended adding surge protectors on unit to prevent electrical surges and power
Call canceled , client got it repaired.
Arrived on site to diagnose a no cooling 2005 Coleman unit. Cons located in back yard. Furnace located in hall closet. Spoke to client and he stated about a week ago his unit would not cool home down anymore. Inspected electrical compartment found primary starter burnt up and worn down. Secondary motor control was dead on fan side and weak out of range on compressor side. Replaced part to test out unit and check full system. Checked start up on compressor are high but still in range. Recommend adding compressor booster kits to help prolong life of compressor and prevent hard start ups. Run amps is pulling 10 amps and max rated at 15. Advised itâ€™s high but in range. Fan motor has been leaking a lot of oil as blades do have oil build up from past. Fan is pulling 1.0 amps and max rated at 1.5. Advised fan could fail in future due to condition. Recommend replacing before completely fails. Checked pressure and are good and cooling hole down now. Unit uses r410a. Went over al findings and
Performed diagnostic on 7 year old Goodman unit. System is not cooling. Blowing only room temperature air. Cycled system for cooling. Checked outdoor unit and found compressor not turning over. Checked system Electrical and found a bad secondary motor control for compressor not allowing it to turn on. Primary motor control is also very burnt and pitted. Replaced secondary motor control to check unit. System cycled on and started cooling. Refrigerant pressures are in range and system is cooling correctly. Homeowner had older mercury style thermostat. Offered options for a digital thermostat. Homeowner approved thermostat replacement and would also like to sign up for maintenance program. Replaced thermostat with T4 thermostat. Cycled system through modes. System is fully operational upon departure. Winter maintenance will be first visit.
Arrived on site to perform AC maintenance on 20 year old Lennox unit. Met with homeowner, her son booked the appointment for today. Cycled System for cooling. Checked indoor unit as well as attic insulation and ductwork. Temperature split is in range and refrigerant pressures are good. No condensation safety switches on drain lines. Secondary condensation line is leaking and there is proof of water stains in the attic. Primary condensate line should be cleared out. Checked outdoor unit electrical and system components. Condenser fan motor looks to be replaced. Secondary motor control for condenser fan motor is extremely weak and out of range. Compressor secondary motor control is within range. Primary motor control is extremely burnt and pitted. Compressor amp draws are in range but high. Pulled condenser fan motor off and thoroughly washed out condenser coil inside and out. Went over findings and recommendations with homeowner. She is fully aware of the condition of the system and any
Performed diagnostic on 20 year old Rheem unit. Met with wife, Spanish speaking call. Homeowner states that system is not cooling. They have had 2 companies come out to do repairs recently. The first company told them That the system was low in refrigerant. They removed the refrigerant from the unit and recharged unit back up but with R407C refrigerant. The unit still did not work after that. Second company came out and found that the indoor blower motor was not even turning on. They replaced the motor and unit is kinda working now but not blowing cold air. Refrigerant charge is not correct as it was charged up without an indoor blower motor running. Compressor is over heating and is pulling 30 amps. Data plate on unit was removed and no information is available on unit. Homeowner also said that secondary line is leaking, but condensation lines are not even accessible as they are in the back side of the coil. Went over findings and recommendations with homeowner. Husband was mildly acc
Performed AC maintenance on a Lennox heat pump. Systems cooling temperature split is 21 degrees. Filter was dirty and changed today. Indoor coils are clear. Indoor amp draws are in range. Outdoor unit was dirty and chemically washed today. Refrigerant levels are a little low. Compressor and fan amperages are ok at this time. System was running at end of appointment.
Arrived on site to diagnose a no cooling unit that keeps on running and dose not shut off. Spoke to client and she stated both if inside and outside work just cools but is always running and never shuts off. Advised I would inspect System and components. Found primary good and a bit worn out. Secondary control is is good. Run amps on compressor are good. Checked pressure and found them to be low. Advised client of findings and she stated she wanted to recharge unit up. Advised would start to charge up and see would see how system good and how the system operates. After charging unit up found unit had a restriction in unit or thermal expansion valve. Also found filter dry to not be operating properly as is restricted and temperature splits before and after are it in range from manufacture specifications. Due to restrictions in refrigerant system is casing system to work way longer and to cool. Advised would be best to replace Thermal Expansion Valve and filter dryer to clear out any con