Cool Air Solutions has provided Hemet CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Hemet CA area neighbors call us first when they need help making or keeping their home comfortable.
for Hemet, CA
Our Reviews by City
Jim - Hemet, CA 92544
Great service with a great and knowledgeable technician
Franco - Hemet, CA 92544
Mike - Hemet, CA 92544
Great customer service!
Rebecca - Hemet, CA 92543
Very helpful n knowledgeable. Highly recommend. Will use Luis for all my maintenance appointments.
Did a great job
Sylvia - Hemet, CA 92543
I was very satisfied
Paula - Hemet, CA 92545
Jeremy - Hemet, CA 92543
Took care of my maintenance check assuring peace of mind. Went out of his way to make sure everything was taken care of.
Karen - Hemet, CA 92545
He was very efficient and educational
Very good service.
Helene - Hemet, CA 92543
Technician very knowledgeable.
Norman - Hemet, CA 92545
Brent was able to get to us sooner than expected. He was personable, professional and really knew his stuff. Thank you so much!
Great, timely, courteous, professional
Greg - Hemet, CA 92545
Was a pleasure having him service my AC.
Harnek - Hemet, CA 92545
Awesome service !
Christina - Hemet, CA 92545
Jorge was very nice, knowledgeable and efficient.
Arthur - Hemet, CA 92545
Very informative! Fixed my issue with my AC unit.
Professional and knowledgeable
Ken - Hemet, CA 92544
Showed me why the age and size of the unit was the reason for high electrical prices
Luis Mendez is TOP NOTCH!!!
Dominic - Hemet, CA 92545
My mom and I can't say enough about Luis Mendez. He knows his stuff. He was very polite and down to earth. TEN stars for Luis!
Roquel - Hemet, CA 92543
John - Hemet, CA 92543
Excellent service great technician
Tim - Hemet, CA 92543
Great Service from Madison
Marcus - Hemet, CA 92545
Great maintenance work and recommended some ways to make our system more efficient
Good tech very knowledgeable
Tim - Hemet, CA 92543
Great customer service
Jesse - Hemet, CA 92545
Very professional, down to earth, straight shooter
Yvette - Hemet, CA 92545
Very respectful polite
Darrel - Hemet, CA 92544
Joe - Hemet, CA 92544
Arrived on site and client stated unit is heating but is not getting to the comfort she wants. Inspected unit and found filter dirty and replaced. Cycled unit and unit is heating just not as warm as she should likes. Found temperature to be off by 2 degrees. Inspect unit inside and out and unit is operating as it should. Unit not getting temp she like. Found unit low on charge. Inspected all connections, inside and out. Bubble tested wields, inspected with leak detector. Was unable to find what is happening. Advised office will be getting a warranty technician out to inspect unit as to what is going on. Unit is heating and client felt it warm for now as unit is operational. No charge for today. Debbie did I not answer and left voicemail and advised office will call her to get back on schedule
Arrived on site to perform furnace diagnostic on 1973 Coleman heater. James stated that he has been consistently real lighting the pilot in the unit and even when itâ€™s lit it tends to shut on and off overtime. Discussed safety concerns with a 1973 furnace and client has been babying unit for the last couple years and heâ€™s more interested in replacement at this point. Supervisor will be Returning upon departure system is non operational.
Upon arrival performed maintenance. Indoor motor and wheel good. Surge protectors in working order. Replaced April air filter. Circuit board and electrical connections in range. Cleaned flame sensor. Cleaned return duct. System is operational. No recommendations.
Upon arrival client stated that system would not do anything. Could have been tripped due to filter being extremely dirty. Last change was last year. Client will purchase own filter. And go up there to replace. System works perfectly fine with no issues. Cycled system of and on. Filter is extremely dirty needs replacement asap. Home owner left for work . No further recommendations.
Upon arrival performed maintenance. Indoor motor looks good, blower wheel extremely dirty. Filter is good. Inducer ampergeas are in range. Circuit board does have stress bubbles. Dusted off electrical components. Electrical was lost up in the attic. Started with the light at the beginning of the attic. I thought light bulb went out. Plugged furnace back in after doing tests. No power coming in. Traced wire back to a junction box. There is no dedicated circuit to furnace. Needs dedicated circuit so that issues does not happen. System is non operational at the moment.
Arrived on site to diagnose a no heating unit. Client is a elderly client with no heat and spoke to caretaker and he stated unit has been acting up since last year. The care take dodo what he could to get unit running then and then did it mess with it until now since itâ€™s cold. He stated unit would shut off and then not even fire up. Upon arrival found unit already opened up as they had someone they knew to come look at it. Called us out since they couldnâ€™t fix it. Cycled heater and found unit not completing the sequence of operation and would shut down. Advised with how unit is acting up told client I think itâ€™s a bad board but wanted to verify to him it is bad indeed. Found no power going to gas valve. Traced back to the molex plug harness and still found no power. By passed the board and gave 24v directly to the gas valve and valve was operational and pushing gas out. Advised client found bird bad as this time I cycle once igniter turned on jumped power to gas valve and the fl
New board installed -Furnace working properly -Heating elements are working
Upon arrival, found system with no power. Replaced transformer and system now has power. Client bought a thermostat that is not compatible with heat pump & auxiliary. Is gonna purchase a new one and program. Will call us if he needs help. System is non operational. But now has power. Could not diagnose further due to thermostat . System is very dirty inside. Client is aware.
Upon arrival furnace was not operational. Found hot surface igniter not energizing. Found furnace ignition module to have failed and it was not providing power to igniter. Furnace is from 1988. Heat exchanger had severe rust inside. Igniter had been replaced and the door switch also needs to be replaced. Advised client on issues. Clients wants to repair unit for now and possibly replace later. Parts will be in stock next week and we are returning to do repairs on Tuesday.
Arrived on site and performed tune up. Found no immediate mechanical issues with furnace. Advised client to retrofit drain line or to have us update it.
Upon arrival performed maintenance. replaced both filters client provided. Indoor blower wheel is dirty and need some cleanings. Indoor motor is running extremely high in amperageâ€™s. Inducer draft motor is running over max amps. Last technician found a possible crack in heat exchanger. Today I went over it again and crack has fully formed. Client is aware of what is happening to the heat exchanger. Turned off the FAU breaker. System is operational. Just running extremely high in energy. Client will see about replacing system .
When I arrived at unit, the furnace was in lock out mode. I reset the unit and turned system on in heating mode. I used door clamp to keep system on while I diagnose. I checked continuity through all my pressure switches. All my pressure switches were working. I took off inducer tube and blew through it of any debris caught in tube. I cleaned flame sensor, just to do a maintenance that was needed on two year old system. I stayed at home for hour and half and didnâ€™t have system shut off. No error codes were provided at motherboard. May be excessive winds shutting off system. System is working and I told owner if it happens again to call front office. Charging $29 diagnostic.
Arrived on site to perform diagnostic on a 2000 york unit. Client stated they just recently tried to fire up unit about a 2 weeks ago and when they turned it on and unit created a loud noise and got worried so shut unit off. Called us out. Jumped on roof and inspect electrical compartment. Jumped unit at the roof units and got heater working. Jumped cooling and found condenser fan motor seized up. Inspect rest of unit. Found primary starter is pitted from operation. Start up is old. Blower assembly and wheel is really dirty. Found blower motor leaking oil and have a lot of oil and dirt build up. Advised motor can fail In future. Advised to client of overall condition and how unit is running and repairs needed. Advised to them now is the time to consider full system replacements due to the age, condition, r-22, repairs and recommendations needed. Compared to full system. Client understands they unit is very old and doesnâ€™t want to spend money into old unit and can still risk failing.
Upon arrival performed maintenance on Lennox system. Cleaned all burning compartments. System was very dirty. Indoor blower wheel is extremely dirty. Advised we can pull out to clean. But we can also add purification to keep system clean and help with air quality . System has no protections.system is operational upon completion.
Upon arrival performed maintenance. Dirty blower wheel, recommended adding purification kits to help system filter more. Client needs to speak to husband about that when he gets home from hospital. Tested all electrical components. System is operational. Circuit board and electricals good. Gas valve In working order. System is operational upon completion
Upon arrival performed Maintenance. Client says he swaps filters out every month or so, advised needs to do an upgraded filtration kit to atleast help system filter more. Blower wheel extremely dirty and off balance. Entire heating components extremely dusty. Cleaned all and dusted all. Client says he wonâ€™t do any repairs do to selling home soon. Will let new home owners deal with it. Advised adding surge protection to system. Says will add GFCI switch. Circuit board does have stress marks . System is operational
Upon arrival client had about 7 programs set on thermostat and Dan to run every 15 minutes. Clients son was messing with it. System is operational. Turned off all programs.
Arrived on site to diagnose a no heating unit. Spoke to client and she stated she tired to turn on heater and nothing happened. Found pilot not on and turned it on. Unit is now operational. Charged for labor at this time. Unit is operational upon departure.
Upon arrival performed maintenance. System is operational. Found UV luv it ballast receiving power but no output. Ballast is 6-8 years old. Ordered from Lennox. System is operational. Replaced filter. Amperageâ€™s and electrical good. System operational.
Darren is here for a turn over, system had cracked heat exchangers, shut gas off again.
Arrived on site to perform heating tune up on a mobile home unit from 1988. Home only have heater client just wanted to it looked at. Cycled it and was operational. Gas was on. Unit had very minimal since it was heat only. Blower assembly wheel is dirty. Motor has been walking oil from pst and has dirt and oil build up. Unit is heating home. Advised unit may have lasted due to it being only heater and not used as much out here. Secondary motor control for blower motor was out of range. Advised no protection on unit. When cycled unit off it took a long time for shut off. Cycled unit and client stated he is not trying to spend money in old unit or replace as he may be planing to move in a couple years. Client just wanted maintenance and inspected. Unit is operational upon departure.
Upon arrival performed maintenance. Indoor motor & wheel are in good condition. Circuit board and electrical connections in range. Filter was replaced client provided. Temp rise in range. System cycled on & off. Gas valve in working order. Wiped system down. System is operational upon departure.
Technician arrived to perform ac tune up -Condenser was thoroughly cleaned out -Filter was replaced -Secondary motor control was reading low mfd, replacement was recommended -Starter chatters, very pitted contact points, replacement was recommended -Refrigerant levels within range -System currently cooling
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. Temp rise of 40-80 needed, I got a temp rise of 53. House heats up to designated temperature. I checked out blower motor of any dirt or debris. Itâ€™s clean, only being a four year old system. Replaced air filter for new air filter. Owner had extra one, so just used his. Thermocouple needed to be lit, got long lighter and turned system on in heating. He never used Heater so he didnâ€™t realize it didnâ€™t work. Ducting done correctly, and all runs intact. Inducer motor is working efficiently. House heats good and ready for winter.
Added a common between indoor and outdoor systems, wired w1 to outdoor for defrost. Monitored operation and tested all modes.