Are you having trouble keeping your San Diego CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been solving these problems since 2006 as we repair, replace and maintain the heating and cooling systems of your San Diego CA neighbors. Call us to find out what we can do for you!
for San Diego, CA
Our Reviews by City
John - San Diego, CA
Amparo - San Diego, CA
Professional rep courteous explained what he did
Greg - San Diego, CA
Cool Air came through once again with fantastic service for my air conditioner. Troubleshooting and repair is their specialty.
Cool Air exceeded expectations
Chris - San Diego, CA
Mateo and Nathan were great. Thank you.
Fred - San Diego, CA
The service was so great what more can I say
Great Complete Timely Install!
Lydia - San Diego, CA
Fast service (next day), and checked everything - but AC still not working right!
Daniel - San Diego, CA
Although tech explained everything he found and recommended - AC is still not working right! Not fixed. Tech said he was calling back tomorrow after talking with manager.
Very Good Product and Value!
Lydia - San Diego, CA
William - San Diego, CA
Chuck - San Diego, CA
Crew was on time and very professional.
Great customer service, knowledge, & patient
Martie - San Diego, CA
John - San Diego, CA
Very thorough and good communication with customer
New install heating and air
Josh - San Diego, CA
Mary - San Diego, CA
Everything was great. Really professional yet personalable
Ty - San Diego, CA
These guys are the best, polite and professional.
Great Informative Service
Carsten - San Diego, CA
Excellen service tech
Kelvin - San Diego, CA
The service tech did an exceptional job checking the units
Periodic inspection of airconditing system
Peter - San Diego, CA
EXCELLENT service. GREAT explanation and quick diagnostic of problem. Prompt arrival.
Randolph - San Diego, CA
Great service as always
Sean - San Diego, CA
Luke and everyone at the Cool Air Solutions Team provided great service as has become expected through the past couple years of having the pleasure of dealing with the company. The installed our Lenox central heat and AC units and aside from a couple minor hiccups did a good job. The service appointments have all gone very well and they stand by their service. Happy to be a continued customer.
Jolie - San Diego, CA
Marvin was professional, prompt, and overall a pleasure to work with. Thank you for sending your best employees to my home!
Robert - San Diego, CA
Tyler was very thorough and reviewed with me item by item what he had done and the results. Took extra time to explain things to make sure that I understood the results.
J - San Diego, CA
Shauna - San Diego, CA
I had Michael come out to do my first yearly AC maintenance check. Had a great experience, just like the first time I called this company when Adam came out. Both technicians were polite, knowledgeable and respectful. I appreciated the fact that they wore booties on my carpet and explained everything they were doing as they went along. Highly recommend this company! Great service 🙂
Sara - San Diego, CA
Arrived back on site to return to do service repairs on 2 Trane systems. Client is aware of repairs is done of 2 Merv racks, 2 plenums, 2 igniter ,2 flame sensors ,2 blower cleanings ,2 secondary motor controls. Client approved of repairs done. Was happy with service. Cycled both systems in heating and cooling both systems are operational. Both systems are operational,heating and cooling upon departure.
Arrived on site to perform fall tune up on 2 2003 trane system located in attics. Client stated no issues and wanted inspection done. Cycled both thermostat and good. Found both filters dirty allowing dirt to enter system. Recommend upgrading filters to merv 16 racks to filter a lot more to both system Would need at add plenums to Seal properly. New flex ducting used and okay. Both blower assembly really dirty creating stress and wear on motors. Recommend assembly cleaning to reduce how hard motors are working and high amp drawls. Amp drawls are in range on both but going to high side as they operate. Motors are staying to leak oil from self wear and stress accumulating and developing over past years. Found secondary motors both out of range and weak from motor draining life of component. Recommend replacing to prevent motor from not operating. Inspected both heat exchanger and found both covered in heat impingement from over heating.no cracks on both just heat impingement all ove
Re wired unit ran test both heat and cool everything works. Showed home owner how to use t stat
Combo Maintenance and installation of Sensi Predict
Performed heating tune up on Carrier system. Met with tenants. Cycled system for heat. Verified proper heating sequence of operations. Checked electrical and heating components. Cleaned off blower wheel assembly as well as heating compartment. Cleaned flame sensor. Ran system through 20 point inspection. Indoor blower wheel is dirty, and motor has started to leak a significant amount of oil. Secondary motor control within range. Gas pipe has no sediment trap.,pulled limit switch and evap coil cover to inspect heat exchanger. Filter is extremely odd size, advised tenant to replace at earliest convenience as it was very dirty. System is operational but is very old and very inefficient. Tried contacting homeowner but calls going straight to voicemail. Will email invoice and findings over. System is operational upon departure.
Inspected outdoor contactor for buzzing. Adjusted low voltage spade connection and tested across coil for proper resistance. Inspected contacts for pitting. Contactor is okay.
Install S30 due to defective Icomfort covered under warranty
Install listed furnace. Replace 5 attic duct runs. Permits and HERS testing included. $7,469 paid to Loweâ€™s. Customer receives $175 from Lennox bringing total to $7,294 0% Finance Options= Loweâ€™s Card 12 months 0% interest or Service finance 18 months 0% interest
Arrived on site to perform fall tune up on a 2017 Lennox system. Furnace and Evaporator coil located in attic. Client stated no issues just wanted filter checked out. Cycled heating mode and system operational. Found new ducting used and good condition. Filter is dirty which is causing airflow restriction in system. Recommend replacing filter to prevent air flow restrictions and reduce amount of dirt entering system. Blower assembly is good light dust. Wheel is good. Blower motor good. Amp drawls on both blower and inducer motor are both good and in range. Evaporator coil is good at this time. Heat exchanger is good. Drain lines are good and draining. Temperature rise is in range and heating. Recommend adding a whole house cleaning and purifying system to help keep system and home clean as well purifying air in home for a better air quality. No protection on high efficient systems. Recommend adding a surge protector on unit to protect it from getting damaged but electrical shortages
Performed AC/furnace maintenance on 2012 carrier system. Upon my maintenance there were a few points or concerns that need to be addressed. 3 ton carrier condenser downstairs- 1. Found a secondary motor control was becoming Week on fan side and hermetic side terminals 2. Condenser fan motor slightly leaking oil from bearing 3. High voltage really showing signs of pitting and burn marks about 90% on contact point 3 ton carrier condenser upstairs- 1. Also found that secondary motor control was becoming week on hermetic and fan side terminal 2. High voltage really showed about 75% pitting and burn marks on contact point 3. Condenser fan motor has leaked out a significant amount of oil from bearing 4. Motor is coming close to over amping from whatâ€™s recommended on specification of data plate. Furnace upstairs- 1. Flame sensor has developed carbon buildup and formed a green coat, This can interfere with heating start up 2. Found multiple heat spots located on heat exchanger due to low
Upon arrival performed maintenance on 1 year old lennox system. Verified system is in working order. Cycled heat on and off. Replaced filter that client provided. Dusted off electrical components and wiped down furnace cabinet. Amperages throughout system are in very good condition. Advised customer to start using merv 16 filter for higher grade filtration. Indoor motor and wheel are in very good condtion. Amp draws on compressor & fan motor are in very good conditon. Refrigerant levels good . Temp splits good. Coils are clean. Dusted all electrical components inside of service door for ac. Secondary and primary motor controls are in very good condition. Was not able to fully wash condenser, water hose was not long enough to get to condenser. Cycled system on and off, system is in very good condition, install good did not need to fix anything . Disconnect and whip good. Fuses good. System was reset tested & fully functional upon departure.
$800 Lennox rebate back to customer brings total down to $25,210
Remove existing furnace and plenum and install new high efficiency Lennox furnace and evaporator coil. Properly plumb drain lines. Clean and flush existing refrigerant lines. Extend lines to existing rooftop pad. Add quad breaker in panel for 220v electrical run to rooftop. Crane service included 25 ft up and 40 ft in. (Crane service will be larked in front of garage 1,2,3 for 30 minutes for the ac lift to rooftop. Loweâ€™s card 5% discount (-$495) after discount $9422.00
Arrived on site to perform diagnostic on 20 year old carrier system. Tenant states that system is not cooling. The breaker tripped last night and he has not been able to reset it back on. I reset breaker off and flipped it back on. Cycled system for cooling. Unit came on and started cooling. Performed evaluation of system to see what had caused the breaker to trip. Primary motor control is burnt and pitted at contact points. Secondary motor control is within range for both compressor and fan motor. Compressor booster kit is still in range and operating. Refrigerant levels are in range and system is producing proper temperature split. Amp draws on compressor are very close to over amping. As the day goes on and it gets hotter outside, amp draw on compressor will also go up and can potentially trip the breaker again. This is due to systems old age and inefficiency. Performed attic inspection. System burner door is missing and no longer on the unit covering the heat components. The system
Tested system for operation. Ran cooling mode and measured temperature splits. Inspected the filter and the safety switch in the attic. Measured outdoor amps and voltages. Tested pressures and battery cap. Found no faults on the system at this time and system is working properly. Tested the heat as well.
Performed diagnostic on 2014 system. System is leaking water on to ceiling. Found a crack in main drain pan at the primary connection port. Because this is part of the drain pan, the whole pan has to get replaced. Can not replace pan without pulling off evaporator coil. Evaporator coil will have to be unwelded and refrigerant would need to be pumped down. Andrew will be quoting and emailing customer a estimate. Emailing information over to Andrew.
WARRANTY. Found battery cap failed. Replaced under manufacture parts warranty. Charged deductible for labor and warranty processing. Unit operational upon departure at this time. Customer declined additional recommendations.
Upon arrival performed maintenance. Outdoor system was washed out. Secondary motor control in range. Refrigerant levels and temp splits very good. Surge protector in great shape. Circuit board and electrical connections good. Signed customer up with esa plan. Filter was replaced. Left extra filter for client. Indoor motor good. Indoor blower wheel has small dirt build up. Evap coil very clean. System was reset tested and fully functional upon departure.
Arrived on site to diagnose problem with current thermostat as client was having issues operating it. Spoke over with client and issues and she stated she was not given a user manual on system. She wanted to also learn how to use system. Now to display current temperature in home. Was able to get client to understand how system work. Client is okay with leaving current thermostat she has. Was able to show her how to operate it and was operational as well show her how to keep set temperature and displays current temperature in home. Gave client info and users manual for her system as well a user manual for her thermostat she currently has. Cycled system to ensure system operating. System is operational upon departure.
Found system to be leaking from drain pan. Drain pan is completely covered with orange built up debree. Causing water to drip from side of drain pan. Per Andrew we do not install these drain pans.
AC MAINTENANCE. Found system operational upon arrival. Replaced hepa filter with customer approval. Blower is clean. Evaporator is clean. Duct is in good condition. Washed condenser coil. Freon levels ok. Temp split ok. Compressor amp draw is good at start and run. Condenser motor amps are good. Bearings are ok. Motor control ok and within range. High voltage transfer relay in good condition. Unit operational upon departure.
Diagnosed the downstairs system and made repairs to the condenser. Tested the amp draws and voltages. Verified refrigerant charge. Did not measure indoor temperature splits (customer request).
Performed diagnostic on 1984 system. Homeowner states that system is blowing air but not cooling. This is a fan coil system. Condenser is on the roof above the 5th floor. Cycled system for cooling. Outdoor unit is not turning on. Checked for power and system is not recieving proper voltage. Found breaker tripped. Reset breaker. Sysyem kicked on and started cooling. Refrigerant levels are in tense and system is producing proper temperature split. Amp draws on compressor are very close to over amping. The hotter it here outside the higher the amp draws will go, which means it will over amp very Quickly. This is most likely what caused the breaker to trip. Compressor is working very hard and is on its last leg. Went over findings and recommendations with homeowner. He is fully aware of he condition of the system as well as the age. System is very old and very inefficient. Homeowner states it hardly gets used and will be preparing to replace it in the future. System is fully operational up
Inspected the system for performance. Tested on both cooling and heating.
Replaced thermostats for outdoor Fujitsu mini split