Are you having trouble keeping your Norco CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been solving these problems since 2006 as we repair, replace and maintain the heating and cooling systems of your Norco CA neighbors. Call us to find out what we can do for you!
for Norco, CA
Our Reviews by City
Fred - Norco, CA
Lyle - Norco, CA
fast and Certious service
Thorough, professional and positive experience
Mike - Norco, CA
David provided excellent service, detailed explanations of areas of concern along with pictures of the attic and under-performing parts for us to discuss. In addition, he provided a full report, along with the readings from his tests. Well worth your investment. He then provided costs for various options, and after researching them on our own, we decided to replace our system.
Performed AC maintenance on a pair of AC pro systems. Temperature split on both systems are in range at 20 degrees. Customer reports bad airflow into the office. Duct run is around 30 feet. Room is on the hot side of the house and is filled with computer equipment. Recommended adding a return. Found a hole in that specific duct run that was repaired today. Indoor electrical amp draws are in range. Outdoor coils were heavily caked in dirt and pollen, they were chemically washed today. Compressor bay and service panel was cleaned off. Start components are in range at this time. Compressor and fan amp draws are reading in range. Filters were dirty and changed today with customer provided filters. Gave a full tutorial to the homeowner on the nest thermostat as well as the app, customer still reports not feeling comfortable with the nest. Homeowners are aware of the importance of maintenance but feel the price is too high. Both systems were running st end of appointment.
Upon arrival Performed maintenance on 14 mini split head units. Washed all filters for systems, washed out condenser coils and outside caging of systems. Cleaned all condensation pump sensors. Recommend replacing 2 condensate pumps as they are non stop buzzing. Evap coils are dirty and need advanced cleaning to keep system running 100% with no restrictions. Replaced filters for clean air system. System is operational upon departure.
Upon arrival performed diagnostic. Reset system code is not there. That code is in reference to Lack of maintenance. Client does not have membership or have done tune up with us .Advised client to let there maintenance technician clean pumps properly and clean coils. Systems are on and running, Excessive water is due to high humidity levels.
Performed AC diagnostic on 2016 Lennox Condenser. Client had stated that system stopped working approximately one week ago. I began my diagnostic at the thermostat and found that the indoor unit is operational and blowing but itâ€™s not cold air. So I went to the outdoor condensing unit I found that it was non-operational. Verified that fuses were intact and found out I was missing a leg of power coming from the breaker. Inspected breaker and found that it was a pushoMatic a very outdated panel. Breaker would not pushing and advised him that he should have an electrician come and verify and replace it. Until breakers are placed unit can be worked on and tested at this point I cannot get power to the system. Client stated that he will have an electrician come and fix it and let us know what happens after that. On departure system is non-operational
Installed nest E thermostat for the bedrooms system. Opened the master bedroom damper to lower the amount of airflow to the back two bedrooms. Set up a sensor in the office. Connected the thermostat to clients WiFi and assisted in setup process. Instructed how to use both thermostat and nest app.
Two system heating maintenance
Cash Discount applied.
Upon arrival performed maintenance. Indoor motor is in very good condtion. Circuit board and electrical connections in good shape. Temp rise good. Duct work is in very good condtion. Filter is new. Gas valve in working order. Heating order of operations good. Cycled heat on and off. Pressure switch good. Inducer draft motor good. Wiring intact. Dusted off all electrical, cleaned inside of furnace cabinet. Attic has very little insulation. Overall system is in good conditon, has new circuit board and blower motor. System was reset tested and fully functional upon departure.
Upon arrival nothing wrong with thermostat, clients concern was fans would turn on. Client had circulation of fan for 30%. Turned feature off. System is operational.
Replace both existing systems complete with listed equipment. Duct corrections. Tie supply duct feeding pool room into the main house system. Tie both existing cut-in supplies feeding office and daughters bedroom into return air of bedroom systems and balance air to force 30% more air into those 2 rooms. 3% cash discount applied
Tested both systems for cooling and measured indoor temperatures. Replaced filters. Inspected outdoor condensers and cleared debris from pad. Cleared dirt and webs from electrical panels and measured system incoming voltages. Measured compressor motor and outdoor fan amp draws. Tested primary run component capacitance and checked starters for pitting. Cleaned outdoor condenser coils.
Tune up and service for both condenser and fau
Furnace trap repair
Upon arrival performed maintenance. Indoor motor and wheel are good. Circuit board and electrical connections good. 20x30x1 filter was replaced. Circuit board and electrical connections good. Temp split good. Gas valve in working condition. System was reset tested and fully functional upon departure.
Performed heating maintenance and performance tune up on both furnaces. Checked all electrical controls. Monitored burners and ignition. Wiped down blower cabinet. Measured amp draws and temperature rise.
Replaced system blower motor under Amanda warranty and replaced clients thermostat with nest. Tested equipment and performed fall maintenance
Two system maintenance and repair in Norco, Ca.
Ac and furnace maintenance in Norco, Ca.
Two system heating maintenance in Norco
Performed routine fall maintenance on amana furnace in norco
Doing a single system air conditioner maintenance out here in Norco
Thermostat replacement in Norco
Air conditioning maintenance and coil cleaning in Norco.
Air conditioning maintenance in Norco