Are you having trouble keeping your El Cajon CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your El Cajon CA neighbors. Call us to find out what we can do for you.
for El Cajon, CA
Our Reviews by City
Same day repair
Richard - El Cajon, CA
Excellent in all respects
William - El Cajon, CA
The sales person offered detailed explanations of our needs and the solutions of the new system. The quote was fair and reasonable and offered sound alternatives such as removal of old and failed insulation, sealing the ducts and the reapplication of new insulation and wrap. None of the other quoting firms offered a similar cost saving alternative. The installer also kept us informed at each step of the process, arrived exactly on time and left the site immaculately clean. Great job !!
Tyler - El Cajon, CA
Great service and price
Victor - El Cajon, CA
Tyler is the best . He called before his arrival was very friendly, knowledgeable and professional. After completing the inspection of our HVAC system he explained to us what he did and showed us pictures as well. Very thorough. I trust and respect cool air solutions and their team and would recommend them to anyone. Thank you Tyler for taking great care of us.
Upon arrival found system low on charge. Did a leak inspection on condenser and found it leaking out the service ports. Replaced service ports under warranty. Added charge. System is now cooling properly upon departure.
Arrived on site to perform spring tune up on 2 2004 Goodman units. Client son was home. Cycled both units and son stated one in has been down for 1 Month and wants it fixed for summer. Had to inspect bigger unit. Found start worn out. Secondary motor control is completely bad. Put a new one in to test if unit operational. Compressor turned off but fan motor did not. Advised fan is seized up. Unit would be needed parts replaced or as far as rebuilding unit to get it operational. Was not able to checked pressure but dose hold R-22. Washed condenser coil inside and out. Found starter worn out. Recommend replacing to prolong life. Secondary motor control is good as it has been replaced in past. Fan motor is leaking oil and is pulling max amps of 1.6 and advised motor can fail. Checked start up amps and compressor has high start up but in range recommend adding compressor booster kit due to age and hard start up to preserve compressor life. Run amps is pulling 9 amps and max at 16. Advise
Performed maintenance on a 2019 Lennox ductless mini split. Both head units are heating over 20 degrees. Drains were checked, filter were cleaned. Outdoor unit was deep cleaned. Voltages and amp draws are in range. Outdoor unit is not electrically protected. Both systems were operational at end of appointment.
Performed mini split diagnostic on 2020 Lennox system. Client stated that the other day condensate was not draining out and It had completely flooded over and started Draining down the side of the living room wall. Original condensate pump was no longer functional and not draining pan out. Replaced with new condensate pump and system is fully operational and draining out properly. Labor and parts were covered under warranty
Replace existing furnaces with listed equipment. Adapt existing cooling systems to new furnaces. Add 5â€ Merv 11 filter kits to furnaces along with new plenums. Remove all duct insulation, seal and re-insulate ducting. Seal existing floor cans. Permits and HERS included. After Lennox rebate total $15,501.00. $300 dollar Lennox card sent directly to customer Financing= 90 days no interest/payment default to 120 Months 6.9% interest 0-down $183 per month
Getting a system up and running out here in El Cajon.
AC Only and fix ducting
Checked mini split for proper operation. Cleaned filters and checked drain pumps. Cleaned outdoor coil. Measured voltages and motor amp draws. Tightened electrical wiring. Tested low voltage
Spring maintnenance on condensor In el cajon
Adjusting airflow for new system, out here in El Cajon
Working on a Lennox package unit out here in El Cajon
Doing a package unit maintenance out here in Grossmont
Doing a package unit heater Maintenance out here in El Cajon
Fall Maintenance 11/26/2018