Cool Air Solutions has provided Homeland CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Homeland CA area neighbors call us first when they need help making or keeping their home comfortable.
for Homeland, CA
Our Reviews by City
Madison's service to his customer is reason for customer's company loyalty.
Victor - Homeland, CA
Promote, so he can be a mentor to promote exemplary customer service standard. He is an asset to your company.
Great service and very thorough.
Regina - Homeland, CA
Professional service. Repair man was efficient & very courteous
Linda - Homeland, CA
On time & efficient
Great and friendly service
Robert - Homeland, CA
Luke was very professional and knowledgeable about the unit. Gave helpful advice on pre-maintenance and Energy efficient ways to save money.
A/C compressor fan & quick release cut-off switch
Bonita - Homeland, CA
Home Advisor recommended 3 names when I needed service on our a/c. I chose Cool Air Solutions after speaking w/Nick & we scheduled service for the following week between 11-1. However the day before my scheduled service, Nick called to remind me of our appointment the next day between '2-4' but I was planning on 11-1. I called him back to correct the time but although he apologized for the error, he said it could not be changed but that the serviceman would be out as soon as possible. The serviceman, Adam, did arrive at 2 & was very respectful, friendly & efficient. He didn't have one of the parts I needed, so had to return to the warehouse to get it. But he promised he would be back & get it fixed the same day. I was thankful he delivered & was good on his word. He completed the job by 5 & was a pleasure to work with & the A/C is working well! The job was very expensive & had I not been pressed for time, I would have called around to find a more reasonable price.
Tanya - Homeland, CA
Professional & polite
LindaZand2000 - Homeland, CA
On time very efficient
Arrived on site to perform diagnostic on a 2014 Goodman unit. Client stated this his rental home. Spoke to client and he stated he bought home in 04 and replaced the unit in 2014. Now they stated unit is not cooling just is producing air flow. Inspected out door unit and compressor was not on. Inspected electrical. Stater is good l. Secondary motor control is really out of range and weak. Advised minimum need part replaced to inspect and see if unit will start up. Put in tester part and got unit to turn on. Compressor struggled to turn on but did crank over and started running. Found unit to be r-22 and is no longer in production. Start up was in range just high from a bad start up. Run amps is good and pulling 7 amps but advised its cold out side so in hotter temperatures outside unit will work harder. Fan motor is in range and working good. Checked pressure and unit is holding a steady charge and in range. No protection on unit. Client is aware of what is going on and he stated he ju
Upon arrival, client said fan motor would short cycle. Unit would heat up to 150 and the fan limit switch would energize the fan motor. The heater would heat between 148-150. Turning the fun on and off. Adjusted the setting to energize the fan at 130. The system is now heating properly. The system is older. Fan motor is in bad shape. Heat exchanger is deteriorating inside from age. It is highly recommended to replace the system for safety. Advised client of findings. Client is budgeting for replacement. Client signed up on maintenance plan. System is operational upon departure.
Upon arrival thermostat was stuck in loading screen, took off mag mount, and hard reset thermostat. System is operational and heating at this time.
Tech arrived on site. Began tune up of unit. Found filter extremely restricted. Replaced with customer supplied filter. Checked indoor motor and airflow. It was good. Ducts are old and dusty. No duck leakage seen at this time. Outdoor coil was hammered. Mostly with dog hair. Cleaned coils and electrical. Checked charge. It was low at this time. Did leak detection in evaporator coil. Could not find anything at this time. Got authorization from management to fill up unit with 1lbs of r410a. Management also said they will extend parts warranty of evap coil until our next visit. On our next visit, we will need to do an isolation test to confirm where the leak is.
Arrived on site to perform fall tune up on a 2016 Lennox system. Furnace and evaporator coil located in attic. Client stated no issues just wanted service. Cycled system in heating. Found filter really dirty due to the area house is surrounded by. Recommend replacing with a Merv16 filter Found new flex ducting and black flex ducting used. Blower assembly and wheel are good just slightly dusty. Motor is good and amp drawls are good and in range. Inducer motor is good and amp drawls. Evaporator coil good. Heat exchanger is good at this time. Blew drain lines out. Slight dirt accumulating in drain lines from dirt that has entered system. All safety switches are operational. Temperature rise is in range and heating. Found system receiving 122.3 voltage. No protection on either unit. Would recommend adding surge protectors on high efficient systems to protect from high voltage that can damage or short out components or damage systems. Cycled system to ensure system operating. Went over summ
Air conditioning maintenance on a Rheem system in Highland Palms, Homeland.
Heating maintenance in Homeland
Heating maintenance in Romoland