Are you having trouble keeping your Pala CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been solving these problems since 2006 as we repair, replace and maintain the heating and cooling systems of your Pala CA neighbors. Call us to find out what we can do for you!
for Pala, CA
Our Reviews by City
Punctual. Thorough. Polite.
Patricia - Pala, CA
Outdoor system not performing properly on arrival, replaced the fuse and tested the voltage and measured the amp draws, the compressor amp draws are high, they are not over the max value but they are higher than they should be. The fan motor bearings are showing signs of wear as well. The capacitor is within range. Recommending the fan motor be replaced and a hard start kit added to reduce the load on the equipment.
Performed AC maintenance on a Goodman condenser. Systems temperature split is 20 degrees. Indoor blower motor is heavily caked in dirt. Scroll wheel has hair and dirt on the fins. Filter is dirty and needs changing. Outdoor coils were heavily dirty and chemically washed today. Compressor start amps are high for this setup. Fan amps are in range and components are ok at this time. Refrigerant levels are ok. System was cycled before leaving.
Mini split maintenance in Temecula, Ca.
Fujitsu Mini Split repair in Pala Ca
Performed Routine Fall Maintenance on 2 Furnaces. Replaced 20x30x1 and 16x25x1 air Filters. Cleaned off grills