Cool Air Solutions has provided Fullerton CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Fullerton CA area neighbors call us first when they need help making or keeping their home comfortable.
for Fullerton, CA
Our Reviews by City
Great as always
John - Fullerton, CA 92833
From the time we found your company, the experience has been nothing but the best. From the install to our most recent six month maintenance .
Tsui - Fullerton, CA 92831
Quick and professional
Thermostat was bad, I bypassed it and system kicked on -New thermostat installed under warranty -System now working properly
Installed gas sediment trap and gas flex -Tested heat, everything is working properly
Upon arrival performed $75 summer tuneup on 27 year old Trane furnace and 13 year old Trane condenser. Found secondary motor control for blower motor is out of limits. Was unable to check temperature split because system does not cool. Cleaned electric filters and metal horsehair filters with water. Found blower motor to be leaking grease. Blower wheel is dusty. Condensation line does not have a P trap, nor a secondary drain. Checked condensation pump and it is working. Performed deep cleaning of condenser coil fins and removed debris. Checked electrical components and existing hard start capacitor is low and out of limits. Dual secondary motor control is within limits. Starter looks fine. Condenser fan motor is pulling 1.1 amps, FLA is 1.3. While checking the refrigerant temperatures and pressures I noticed it is low on charge. Subcool was only 1.8 and required is 13. The owner does not want to move forward with any repairs. Upon departure system is not cooling.
Ac maintenance on a Carrier system in Fullerton.
Performed routine fall maintenance on lennox furnace in Fullerton.
Furnace maintenance in Fullerton
Performed full system rejuvenation in Fullerton.
Radio promotion service a.c. and heating in Fullerton
Doing an air conditioner maintenance out here in Fullerton
Winter maintenance on lennox furnace
Performed Routine Fall Maintenance on Lennox Furnace. Inspected duct work and electrical components.