Are you having trouble keeping your Perris CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been answering these questions since 2006 as we repair, replace and maintain the heating and cooling systems of your Perris CA neighbors. Call us to find out what we can do for you.
for Perris, CA
Our Reviews by City
Rolando - Perris, CA
I am satisfied with him, thank you
great efficent service
Bob - Perris, CA
The Tec was very knowledgeable and pleasant to deal with.
it is great service and awesome price
Jonigodlove@gmail.com - Perris, CA
YOUR COMPANY, OFFICE PERSONAL AND FIELD PERSONAL ARE WESOME I THANK YOU ALL FOR YOUR COURTESY AND KINDNESS. JG.
Avacon - Perris, CA
Always professional and helpful
A little pricy
Norm - Perris, CA
Luke was great. He wasn’t given the correct size filter for my hallway.
Michael was great. He has a great disposition and very friendly.
Norm - Perris, CA
Fehrnando - Perris, CA
AC/HEAT MAINTENANCE. Found system operational upon arrival. Replaced standard 20251 filter. The filter that was in there before the maintenance was past due and restrictive. Blower clean. Evaporator clean. Burners and burner cabinet clean. Gas pressure ok. Inducer ok. Limits and switches operational at this time. Board ok. Flame sensor ok. Igniter ok. Temp rise ok. Static ok. Washed condenser coil. Freon pressures ok. Temp split ok. Motor and compressor amps ok. Motor bearings ok. Motor control is within range at this time. High voltage line relay in good condition. Unit operational upon departure.
Jimmy installing secondsryncomtrol
Upon arrival found system low on refrigerant. Advised customer we can charge system up with refrigerant, declined gonna think about replacing system will give us a call back.
Customer canceled due to thinking we were his home warranty company. Meant to cancel us but canceled his home warranties.
NO COOL. Found system non operational. Customer stated unit doesnâ€™t run after changing the batteries. Checked thermostat and saw battery compartment is separate and very accessible without removing thermostat. Checked for power and found no low voltage coming out of low voltage controller. Would have to check if manufacture still has this part due to the age of the system. Due to age and condition of the system we highly recommend replacement options. Customer will talk it over with the dad and sister to find out if they want to move forward with replacement options. Customer will call us when he knows. Unit not operational upon departure.
CALLBACK/WARRANTY. Customer stated unit is still leaking water. Says tech was out here yesterday and said he didnâ€™t have all the parts to fix it so he only put glue on the leak. Checked line and it was overflowing at t connection to p trap. Cut line open to pressurize. Blew out rocks and gunk out of the line. Also used nearby hose to clean inner lining. Removed damaged connection and went home supply store to get new one/s. Flushed line with over 2 gallons to test. Line is cleared upon departure.
Replaced the thermostat, repaired the primary condensate line and cleared the line. Added a trap and safety switch to the condensate drain.
Performed AC diagnostic on 1995 comfort maker condensing unit. Upon my diagnostic I found that the system was on although would shut off after about 15 minutes. This has been caused due to the compressor going off on thermal overload and the pressure relief valve releasing pressure due to high amounts building up. 3.5 ton Comfortmaker- 1. Compressor going off on thermal overload and opening pressure release valve. Windings within compressor are overheating due to insulation thinning out. Compressor is on borrowed time and occurs at the end of compressor life. 2. System contains R22 refrigerant Which has been completely phased out as of January 1, 2020. 3. High voltage relay showing signs of pitting/burn makes on contact points about 95%. 4. Compressor pulling incredibly high amperage at 21 A with max rated amps on data plate are only 19.2. This is also the reason why the compressor is failing due to high energy consumption in overworking. Recommendations- 1. Replacement of R22 3.5 ton
Replacement of condenser and coil with Lennox Equipment Re-insulate exposed ducting in garage.
Arrived on site to diagnose a non operating system. Clients had home warranty out and could not fix issues. Stated they had a shortage due to past owners dog chewed up condenser thermostat wires. Upon arrival system would. Or operate or have power coming in. Thermostat is bad and failing already recommend replacing thermostat. Found system with no filter as it was in the return plenum as it was not the right size and fall in. Found blower assembly hammered, and blower wheel dirty, motor is leaking oil and has layer of dirt and oil.Found someone has bypassed the Low voltage door switch as it it currently cut off. Advised that is a safety concern. They need that replaced or repaired immediately. Test for voltage was not getting none but was getting 120v at pig tail plug in. Replaced a transformer and now had power in furnace as I got blower motor working and operational. Went to out door unit found condenser thermostat wires were chewed up and exposed causing electrical shortages and why
Post job walk
Performed AC maintenance on 7 year old carrier system. Cycled system for cooling. This is a single stage system that is split off into 2 zones. Checked outdoor unit electrical and system components. Amp draws on compressor is in range. Amp draws on condenser fan motor are over amping. A lot of oil loss is present on condenser motor. Pulled condenser motor to thoroughly wash out condenser coil inside and out. Secondary motor control is in range. Primary motor control is in good condition. Refrigerant levels are in range and system is producing a good temperature split. Replaced 1 inch filters. Went over findings and recommendations with homeowner. Cycled system, system is operational upon departure.
We will be installing a used 3.5 ton Goodman ac and coil. Model GSX16. This also includes a filter rack under the existing furnace with a condenser pad and service disconnect. Also included will be a a filter dryer to filter contaminants switching from r22 to r410a. We will use rx11 flush kit to clean all the old Freon out so that we can use the new r410a Freon. Evaporator coil will have an emergency drain sensor to protect against flooding
Performed diagnostic on 2003 system. Homeowner states that system is leaking water in her bathroom and in her hallway. Bathroom ceiling has almost completely caved in and hallway is getting stained with water as well. Went into attic to inspect system. Performed thorough inspection of system, findings are as follows 1. Main drain pan is over flowing, leaking water over and into bathroom and hallway 2. System is not leveled correctly, which is causing all the water to towards the back of the drain pan and over 3. No water is making it to the drain lines for this reason as well 4. Evaporator coil is completely clogged up. 5. Seems like there was a rope tied around the drain pan to prop it up so that water would flow through the drain pan 6. Ducting is in horrible shape. It is not sealed correctly and ripped in numerous parts. Went over all findings and recommendations with homeowner. Gave her some repair options but mentioned that no warranty can be given on any work done based on
Upon arrival performed diagnostic. System does not cool properly. Found system icing up on refrigerant lines. Evap coil is dirty and causing air restrictions. Blower wheel is completely covered in dirt & debree. Indoor motor is leaking oil and has a lot of dirt covered in it. Outdoor fan motor leaking oil. Compressor is freezing up due to restrictions inside of system. Recommend replacing system due to age and inefficiency & cost of repairs.
Upon arrival performed diagnostic. System turns on. Pressures are completely flat. Refrigerant levels are really low for system. Darren coming out on Saturday to give replacement options.
Installed customer supplied thermostat. Rewired for common wire to be operational. Cycled system through heating and cooling modes. System is fully operational upon departure. Offered to do a thorough evaluation of system , homeowner did not want me to and said system has been running fine, only thing he needed was thermostat installed.
Quality control check
Performed Ac maint on 2008 Lennox system. Cycled system for cooling. Checked outdoor unit electrical and system components. Amp draws on compressor and condenser fan motor are fairly high, but within range. Secondary motor controls are in range, primary motor control is in good condition. Amp draws on compressor start up are high. Pulled condenser fan motor to thoroughly wash out condenser coil. Condenser coil is really deteriorated at a couple different spots and refrigerant lines are very exposed. Reassembled unit. Replaced 1 inch filter. Checked indoor unit electrical and system components. Blower wheel is starting to accumulate dust. Could not access attic due to full closet. Refrigerant levels are in range and system is producing a good temperature split.
Drop cloths on any traffic area- Shoe covers will be used- painters plastic around the attic access will also be used While performing work- Ducts have a limited lifetime warranty on parts and workmanship.
Upon arrival performed maintenance. Replaced2 blower motors and battery caps. Performed cleanings on system. Installed 2 air scrubber to maintain cleanliness throught system and help with odors, dust levels, pet dander, and have purified air inside of home. Surge protectors to keep system healthy. System was reset tested and fully functional upon departure.
Heating maintenance in Perris, Ca
Ac tune up in Perris, Ca.
Ac diagnostic and repair in Perris
A.c. maintenance in Sun City