Heating, AC & Indoor Air Quality
Cool Air Solutions has provided Vista CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Vista CA call us first when they need help making or keeping thier home comfortable.
for Vista, CA
Our Reviews by City
Nancy - Vista, CA
Knowledgeable technician and open to explaining service
Nancy - Vista, CA
Truly great service. Both technicians were friendly and professional.
Michael was great
Nancy - Vista, CA
Michael was great.....professional, friendly and knowledgeable. Highly Recommend!!!
Diane - Vista, CA
On time and professional
Nicole - Vista, CA
I appreciate Luis and his pleasant demeanor
Robert - Vista, CA
Michael did a great job. He was on time and got the job done quickly.
Linda - Vista, CA
Jeremy - Vista, CA
Jorge is a great technician with exceptional professionalism, I couldn’t have asked for better service!
Denise - Vista, CA
Paul - Vista, CA
Pamilla - Vista, CA
Mary - Vista, CA
Came to do A/C, H/V tuneup, but suggested to wait since ducting needed repairs. Arranged for a senior technician to come out and inspect further. Did not charge.
Barbara - Vista, CA
Had a great experience through the whole process! Jordan was an awesome sales rep. Very professional and knowledgeable! Jordan knew what would work best for our small house and budget. Installers Freddie and Miguel were amazing! Very efficient, clean and professional. Communicated wonderfully through the whole process. I couldn’t be more pleased with my purchase and the installation process. It’s my pleasure to give them a FIVE STAR 🌟🌟🌟🌟🌟 Review! I will highly recommend this company to others I know. Thank you!
Mike - Vista, CA
Mike - Vista, CA
Joe - Vista, CA
Great service. Trevor went above and beyond.
Debbie - Vista, CA
From the ease of scheduling to the friendly reminder the day before the service, everything was easy and fast. My service tech Trevor was great. Called when he was on his way and again when he was close by. Explained everything to me and made great recommendations. He even helped me get a mouse that had ran into my house out! You don’t find service like that anymore.
Could not ask for better Service
Maintenance - Vista, CA
I have had several companies who have provided simul[ar service. None were as professional as Cool Air Solutions. The Adm staff were great making timely calls to schedule service, arrange appointments and confirming the techs time etc. Could not be more pleased....Paul G in Vista
Great service, as usual!!
Rick - Vista, CA
Fred - Vista, CA
Luke was great! He was very friendly and answered all of are question. Hope he comes out next time.
Good response to warrant need
Garth Hall - Vista, CA
Technican was friendly and competent.
Very helpful with information.
Linda - Vista, CA
Luke a bit late but very apologetic-not a real problem. We are trying an adjustment to thermostat to see if that helps the situation of heat coming on 2 hours before scheduled. Luke helpful with explanation and very courteous. I will call cool Air if problem does not improve. Thank you.
CarolPedro - Vista, CA
The young man, Nick Wilson who came to service our unit was very respectful and clean cut which is important to me. He was professional and very informative, taking the time to explain the workings of the unit. Definitely a good reflection of the company he works for!
John - Vista, CA
Excellent service Explained process and services On time, very courteous
Becky - Vista, CA
We were given very good information and great advice
Charged system with freon and added leak sealant plus leak detect ant. Need to come back in 4 weeks to trace and locate leak in split system. Unit operational and cooling upon departure.
Performed diagnostic on system. Age unknown, model and serial numbers are no longer visible but unit is old. Business owner states that they just leased the business space not too long ago, and that a month or two ago had someone out to refill it with r-22 refrigerant. Previous business owner left them a full jug of r-22. System has prior history of having a leak. Current owner is aware of it but only wants to do the minimum as he is only leasing the property. After diagnosis, found that compressor was not turning on due to a bad secondary motor control. With approval, went ahead and added new secondary motor control. Cycled system, compressor kicked on normally. System is now cooling and condenser producing good temperature split. Homeowner is aware of the condition of the system, and knows that system will eventually need to be recharged, or replaced. System is fully operational upon departure.
Post job walk
Arrived on site to diagnose a no cooling 2020 Lennox system. Upon arrival client stated system dose work and is just not cooling as good as she thought it would. She cycled cooling mode on indoor unit was operational condenser was operational. Went to check Indoor unit. Checked ducting, filter condition, evaporator coil and all was good and clean. Checked refrigerant pressure and system was low as it was only cooling in a16 degrees split. Advised client I would need to charge system up to get it were data plate specifies. Charged system up with a pound and Half. Got good pressure and got sub cooling up to 7.6 as when I first checked it was at 0.6. Checked temperature split and system is now cooling at a 19 degrees split. Advised client That she dose not have an insulation in attic and the heat load is going into home due to no insulation. Client is also aware her house has a lot of windows and the sun is always hitting house sunrise and sunset and allowing heat load to enter home.
Found system operational upon arrival. Customer washes filter himself and did not want me to wash it. Checked blower. Amperage was ok but motor control is failed and may cause motor to fail. Blower wheel is dirty and accumulating dirt. Evaporator coil is slightly dirty. Washed condenser coil. Checked motor controls. Compressor and condenser fan motor control is rusted. Condenser fan motor is rusted on exterior and leaking at the bearings. Compressor amps are low. After checking freon levels found out the reason why the amp draw is low is because freon pressures are low. With the freon being this low it is highly likely there is a leak somewhere in the system. Found no obvious leaks with a quick leak search. Customer approved adding freon and sealant. Need to come back tomorrow to finish charging system. Ran out of 410 and there was nobody open or near the area to supply me more. Unit running at this time but needs more.
Pull clean and sanitize the indoor blower motor. Replace the outdoor fan motor. Replace the starter and add a compressor assist kit. Replaced outdoor fan motor, starter and added compressor assist kit. Cleaned the outdoor condenser bottom and coils. Blessed blower motor wheel, housing and blower cabinet. Wiped inside cabinet and vacuumed. Wiped motor and circuit board / wiring. Tested system before departure, system functioning properly at this time.
Upon arrival found compressor to be icing up. King valve has restrictions. Have a 13 degree difference from one side of valve to another. Indoor motor leaking oil and covered in dirt and debree. Outdoor fan motor leaking oil. Primary power distributor pitted and burned. Secondary control low. Was not able to do full maintenance due to system not working properly. Customers want to have full system options before going with repairs. Darren to come out tomorrow between 12-2 for replacement options
Total after all rebates is 11148 Financing promotions: 18 months no interest or Reduced 6.99% fixed apr at 133 per month
Arrived to perform a combo tune up heat and ac for a non member customer. Checked readings on motor, static airflow pressures and temperature rise. Pulled blower assembly out, showed customer the dirty blower wheel. Inspected heat exchanger. Evap coil looks good. Reinstalled assembly. Declined to clean for now. Flame sensor is good, gas pressures within limit. Installed new 14x25x1 filter. Cycled system off and on. System is operational upon departure. Outside unit checked primary motor control looks good, no burned or pitted contacts. Secondary motor control in range. Disassembled unit, sprayed chemicals inside and out, washed completely down. Checked compressor start up amps, compressor run amps and fan motor. Refrigerant pressures are within limit. Cycled system off and on. System is operational upon departure. Recommendations- sign up for our maintenance plan, receive two visits a year free filter change and receive 20% discount on upgrades or repairs. Chemically clean blower asse
Replace cooling only system. Adapt new evaporator coil to existing furnace. Install new Digital programmable Honeywell T4 thermostat.