Let Us Make You Comfortable
There are plenty of heating and air conditioning companies out there that claim to have great value and great technicians and maintenance plans galore. But what do those companies really know about Vista and its neighbors?
At Cool Air Solutions, we understand what it takes to build a strong relationship with a customer and that’s trust. Because we want your trust, we always act with your best interests and safety as our first priorities. You will never find you’ve been overcharged or that our work is shoddy and incomplete. We’ll work with you like you are a member of our very own family and that’s not just talk.
Check out our reviews to see what your Vista neighbors and neighbors nearby think of their experience with Cool Air Solutions and then call (888) 659-2665 for the best heating and air services in the area.
How Can We Help With Your AC or Heating System?
We offer a number of services, including:
- Heating Repair
- Heating Maintenance
- Heating Replacement or Installation
- AC Repair
- AC Maintenance
- AC Replacement or Installation
- Deals & Specials
All of our heating and air conditioning services are guaranteed to leave you 100% satisfied. Our energy efficiency skills can help you save the environment and your bank account. Our indoor air quality and in-home virus control systems take on the pollutants that sneak into our home’s air systems.
What’s the Big Deal About Maintenance Plans?
If you’re a member of our Comfort Club, you’re privy to deals and prices our non-member customers can’t access. By checking out your system twice a year and performing needed tune-ups, you lengthen the life of your heating and air conditioning system. You also prevent surprise repairs such as an AC shutting off in the middle of the hottest week of the year.
Don’t Take Our Word For It
In our tech driven world, there are a million ways to pick who you will do business with. Our philosophy is that no matter what we say, our actions are what proves our commitment to you. Read about our services and check out what locals think of them, so you can learn for yourself that Cool Air Solutions is the top-rated heating and cooling company in your area. Once you’ve checked us out, give us a call! We’d love to hear from you. (888) 659-2665
for Vista, CA
Our Reviews by City
Jeff - Vista, CA
We have been using Cool Air Solutions for years. Michael did a great job of making sure that his work was just right! Highly recommended!
He was professional and did a great job
Garry - Vista, CA
Joe - Vista, CA
Jane - Vista, CA
Luis was fabulous. He stuck with it until the answered was found. I would highly recommend him.
Awesome Service Rep
Ray - Vista, CA
This is my 2nd time dealing with Micheal and both times have been a very pleasant experience. He is very knowledgeable and does a great job explaining things. I’ve thoroughly enjoyed my interaction with Michael both times. Keep up the great work Michael.
Very fair pricing
Dana - Vista, CA
Louis was able to fix my older AC and now it works great! About an hour into his visit I was worried but he persevered and got it running at an incredibly decent price. They will now do all my heating and AC service.
Richard - Vista, CA
Madison did very well. He was knowledgeable and well prepared. My only issue was the scheduleing, there was some confusion about the arrival times and the date of the appointment. This was in the office; Madison had nothing to do with the confusion.
Super and professional, caring service
Stephanie - Vista, CA
Madison is a caring perfectionist who knows his stuff and offers unbiased and informed suggestions. I’m so glad he was the technician who worked to get my system working. I recommend him 110%!!!
Dan - Vista, CA
Dustin - Vista, CA
Nancy - Vista, CA
He was wonderful and very informative about air purification
Great Service and Courteous
Melrose - Vista, CA
All I can I am a Happy camper!
Patricia - Vista, CA
I have been using Cool Air solutions for my furnace/ AC unit since I bought my home in 2017. The employees have always been polite and courteous. They have always tried to explain what they are doing and how the system is working. Most recently I had an employee by the name of Daniel Tietze do the routine maintenance on my units. Not only did he explain everything but he also took pictures to show me what was happening and wrong with the furnace in my attic and why my AC was noisier than normal. He also helped me to get a better fitting filter in place. Truly a wonderful and professional person and it was a painless experience. I learned a few things too. Thanks so much for taking care of my home and my family.
Jane - Vista, CA
Luke did a fine job servicing my heater.I appreciated his efforts to abide by the Covid procedures while he was here. Very polite and friendly. Thank you Luke. Jane Gorsky My husband Paul passed away 12/10/2019. Please update your records to my name..
Great service and friendly 😊
Melrose - Vista, CA
Explaining everything done, and got our unit up and running yay😊
Dan - Vista, CA
Very prompt. Very professional. Got the job done on the 1st visit. Did not try to upcharge..
Mike was great--explained everything well
Gene - Vista, CA
Great service and very educational.
Robert - Vista, CA
Michael, arrived in time as scheduled. I appreciate him calling to confirm if the scheduled time was still good. Very informative and thorough in his diagnostic. Highly professional and courteous. Inspected the heating and a/c unit and fixed or gave recommendations on what will require replacement. Explained every step he was doing to me, which kept me informed and at the same time, made me learn more about the process. I would highly recommend this company again and will continue to do business with them.
Dana - Vista, CA
Jorge Was very friendly and knowledgeable. I appreciate the job that he did.
Knowledgeable, extremely informative
Kathleen - Vista, CA
Michael was very professional, gave me the straight poop on the condition of the heating system. We talked options, there was no pressure just a factual discussion. I very much appreciated working with him. Plus he likes cats!
Give Jimmy a raise!
Susan - Vista, CA
We have had Jimmy come out twice now and his professionalism and expertise is blaring. Last night he was here at the end of his day and he was as energetic as if it was the beginning of the day. He walked us through everything he saw with our furnace. We really really appreciate that he was not pushy in selling us on repairs but instead was able to show priority repairs which is great for a layman and the anxiety that come with lacking knowledge in this area. You want to keep Jimmy in your company for sure ,he will bring in good business and give you a good reputation. I’d give him a raise!!
They we’re very nice and helpful. Explained everything very well.
Lluvia - Vista, CA
The motor I had to buy was pricy for me but if I had to buy it for it to work.
Great talent, good service
Bill - Vista, CA
Debbie - Vista, CA
Had great service
Great service and friendly
Ricky - Vista, CA
Inspected the systems airflow and drew up a duct map to make recommendations to balance the home.
Tech arrived on site. Performed furnace tune up. Client had replaced his entire system recently. System was clean and install was up to code. Tested all electrical components, static, and temperature rise. All checked out.
Tech arrived on site. Performed ac tune up. Cleaned condenser coils and inspected motors. Condenser motor is leaking oil. Checked electrical. Components are okay. Refrigerant charge seemed low at the time due to outdoor temp being low. Temp split is good. System is running on an obsolete refrigerant. Attic ducts are Iâ€™m good condition. Filtration is poor. Lots of dirt getting into the unit. Flushed out drain lines. No form of flood protection is currently installed. Unit is operational upon departure.
Customer is going to pay with a check
Upon arrival, replaced all 4 filters. Condenser fan motor control is weak. Evap coils are extremely dirty and need cleaning. Thermostat in working order. Amperages are not so efficient. System is running on higher side of electrical. Temp splits good. Blower wheel dirty. System is operational, client gonna get a hold of land lord. For repairs .
Inspected the systems airflow and drew up a duct map to make recommendations to balance the home.
Performed AC and Fuenace maintenance on a Lennox system. Burner operation was checked. Flame sensors and limit switches were cleaned and verified in correct working condition. Filter is ok. Heating temperature split is in range at 33. Blower compartment is clean and spinning freely. Outdoor unit was chemically cleaned. Compressor bay and service panel was cleaned. Refrigerant levels were verified in range and recorded. Starting components were measured. Compressor and fan amp draws are good. System was running st end of appointment. Customer had questions about thermostat. A full tutorial was given for the sensi thermostat and customer is happy at end of appointment.
Performed Ac maintenance on Lennox condenser.
Performed AC maintenance on a Lennox condenser. Upon arrival customer reports poor airflow to a single room. This room is a home office with equipment, 1 small register. Did full duct inspection using 3 separate attic accesses. Ended up adjusting airflow to that zone in the s30 thermostat and also adjusting a register to push more air. Filter is dirty but customer is going to purchase his own. Outdoor unit was deep cleaned and given a tuneup. All data was recorded. Customer signed up for monthly maintenance to keep system working at a standard. Unit was working at end of appointment.
Condenser may be on back order, until installation Cool Air Solutions is liable to keep systems up and running until installation
Upon arrival performed diagnostic, found compressor to not be kicking on for cooling mode. Found secondary control to be out of range. Replaced and got system gojng. Temp splits in range. Client needs to move fencing around condenser so we can do a tune up. Filter is extremely dirty and needs t0 be replaced. Client signed up for maintenance program. System is operational upon departure.
Performed AC maintenance on a Lennox system. Customer recently changed filter. Electrical connections and starting components were verified in range. Refrigerant levels were verified. Outdoor unit was chemically cleaned. System was running at end of appointment. Customer is very happy with the performance of the system and also with cool air solutions.
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser, customer declined condenser cleaning service today due to company. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor furnace unit. I measured temperature splits. I checked condensates for proper drainage and safety. Filter was changed. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Upon inspection of both units, I found there to be no electrical protection on either, recommend having surge protection added to protect sensitive electrical components. Upon departure system is working and operational.
Arrived on site to diagnose a no cooling 2003 unit. Condenser in back yard. Client stated they lived i home for 5 years and few days back unit stop blowing cold air. Cycled unit and both indoor and out door unit both were operational just blowing warm air. Inspected electrical compartment components. Found secondary completely bad and primary starter was burnt up on contacts and is original to home. Highly recommended replacing both to keep system operating. Replace secondary and ran system. Checked start up amps and are high due to age and inefficiency. Recommend compressor booster kit to help prevent hard start up and help prolong compressor life as much as possible before it fails. Run amps is pulling 13 and max rated at 18. Advised compressor working hard from age and operation. As it is on borrowed time. Checked pressure and found unit to use R-22 thatâ€™s no longer In production. Pressure are stable and cooling hole at 18 degrees. No protection on unit and recommended adding sur
Return for Service: Blower Housing Pull and Clean Upon arrival system is working and operational. Removed blower housing from unit, taking care to disconnect and reconnect fan motor as well as moving control board for access. Proceeded to take the housing outside and wash with water and chemical solutions removing dirt and debris from the scroll wheel and housing, reinstalled and tested to confirm proper operation. Upon removal of housing I found the blower motor to be leaking oil as well as have shaft play, informed member of pros and cons of replacing blower motor. Upon departure system is working and operational.
Performed diagnostic on 15 year old system. Homeowner states system is not cooling and outdoor fan is not spinning. He did try to buy the parts but they would not let him without a contractor license. Cycled system for cooling. Indoor unit kicks on and blows air. Outside the compressor turns on but the condenser fan motor is not spinning. Checked outdoor unit electrical and system components. System is getting all proper voltage. Found a bad secondary motor control that was not allowing fan motor to turn on. Was also low on hermetic side. Put in a temporary secondary motor to fully inspect system. Cycled system on and system started cooling. Refrigerant pressures are in range and system is cooling correctly. Amp draw on condenser fan motor is above itâ€™s rated capacity. Compressor amp draw is in range. System is older and working inefficiently but is still cooling. Went over all findings and recommendations with homeowner. He is fully aware of the condition of the system and any conce
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution, removing dirt and debris. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor furnace unit. I measured temperature splits. I checked condensates for proper drainage and safety. Filter needs to be changed, member said they will go purchase and install. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Upon inspection of the indoor furnace unit, I found the secondary motor control to be leaking castor oil and to be far below its rated values, as well as the blower compartment to be heavily laden with dirt and debris. Recommended and replaced motor control, and on the 15th of September are comin
Performed AC maintenance on 8 year old system. Cycled for cooling. Checked indoor and outdoor unit electrical and system components. Replaced filter. Pulled outdoor condenser fan motor and thoroughly washed out condenser coil inside and out. System is operational upon departure. Did speak to homeowner about Air Purification system buyback program, wants to hold off today.
Performed AC maintenance on a Lennox condenser. Systems cooling temperature split is 16 degrees. Indoor amp draws are ok. System has history ofn leaks, inspected evaporator and condenser with a UV light with no findings. Outdoor unit was dirty but chemically washed. Start and run amps are high, recommending an assist kit. Refrigerant levels are ok at this time. System was running st end of appointment.
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution, removing dirt and debris. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor Air handler. I measured temperature splits. I checked condensates for proper drainage and safety. Filter was changed. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Upon inspection of outdoor condenser I found the compressor to be pulling high amperage upon start up, recommend adding a compressor saver kit lower wear on compressor as well as lower start up amperage. Installed compressor saver kit on system. Upon departure system is working and operational.
Upon arrival performed maintenance on hvac unit. Washed outdoor coils off completely. Secondary motor control is in range. Primary starter good. Tested disconnect fuses. Advised client compressor is pulling 146 amperages , Max of 150. Recommended booster kit to bring amperages down in range. Ducting is strapped correctly, do not see any kinks or damages. Attic insulation in good condtion. Condensate pump in working order. Running amps on compressor in range. Condenser fan motor is showing signs of Leaking oil. Refrigerant levels are in range. System is operational.
Upon arrival performed maintenane, cleaned entire system out washed coils completely. Amperages on system are in range. Filter is good, next visit needs change. Circuit boards are in good condtion. Recommend adding surge protector to keep system protected. Indoor motor and wheel good. Indoor coil clean. Ducting is in very good condition. Thermostat in working order. System is operational. Client would like to use card on file for esa. She said please send her anything she needs to sign for comfort club, was doing work outside.
Upon arrival performed maintenance on hvac system. Found system to have a lot of new parts. System has been rebuilt. Condenser fan motor in range. Primary start component good. Hardstart in working order. Refrigerant levels in range. Temp split good. Filter has been replaced. Client would like to install nest next visit w cleaning. Dusted off all electrical components. Compressor running in range. System is older but cooling. System operational.
Upon arrival performed diagnostic. Found system to be losing power at contactor for a split second. Nest thermostat was dead and transformer was dropping power. Added a 70va transformer and system is performing, not losing power anymore .
Found failed secondary motor control & burnt wiring on outdoor condenser, clogged indoor filter and booster installed on unit.