Let Us Make You Comfortable
There are plenty of heating and air conditioning companies out there that claim to have great value and great technicians and maintenance plans galore. But what do those companies really know about Vista and its neighbors?
At Cool Air Solutions, we understand what it takes to build a strong relationship with a customer and that’s trust. Because we want your trust, we always act with your best interests and safety as our first priorities. You will never find you’ve been overcharged or that our work is shoddy and incomplete. We’ll work with you like you are a member of our very own family and that’s not just talk.
Check out our reviews to see what your Vista neighbors and neighbors nearby think of their experience with Cool Air Solutions and then call (888) 659-2665 for the best heating and air services in the area.
How Can We Help With Your AC or Heating System?
We offer a number of services, including:
- Heating Repair
- Heating Maintenance
- Heating Replacement or Installation
- AC Repair
- AC Maintenance
- AC Replacement or Installation
- Deals & Specials
All of our heating and air conditioning services are guaranteed to leave you 100% satisfied. Our energy efficiency skills can help you save the environment and your bank account. Our indoor air quality and in-home virus control systems take on the pollutants that sneak into our home’s air systems.
What’s the Big Deal About Maintenance Plans?
If you’re a member of our Comfort Club, you’re privy to deals and prices our non-member customers can’t access. By checking out your system twice a year and performing needed tune-ups, you lengthen the life of your heating and air conditioning system. You also prevent surprise repairs such as an AC shutting off in the middle of the hottest week of the year.
Don’t Take Our Word For It
In our tech driven world, there are a million ways to pick who you will do business with. Our philosophy is that no matter what we say, our actions are what proves our commitment to you. Read about our services and check out what locals think of them, so you can learn for yourself that Cool Air Solutions is the top-rated heating and cooling company in your area. Once you’ve checked us out, give us a call! We’d love to hear from you. (888) 659-2665
for Vista, CA
Our Reviews by City
Michael was awesome!
Barbara - Vista, CA 92084
Communicated awesome about arrival time… explained the repair/charges. Was very efficient and professional. He represents your company well! 🌟🌟🌟🌟🌟
David - Vista, CA 92084
Thorough service and professional employees!
Kevin - Vista, CA 92084
Tony did a thorough, excellent job. He was very professional and explained to me the answers to all of my questions.
Ron - Vista, CA 92083
Great job. I will definitely recommend the company to my family in Carlsbad.
Excellent service, very good price.
Chris - Vista, CA 92081
Luis M. diagnosed the problem with my heating system, located the parts needed for my repair, got the parts in his hand the next morning and installed them. He started up the system and did a field check before noon the next day (all in less than 24 hours). I could not ask for more. Thank you Luis.
Jo - Vista, CA 92084
Dennis - Vista, CA 92081
Tech was friendly and courteous
Quick response, quick solution
Oliva - Vista, CA 92084
very well done summation of furnance needs
Gene - Vista, CA 92081
Sara - Vista, CA 92084
My technician was great! The customer service with regards to arrival by both the office and my service tech was great. Brent, the tech helped expidite the problem and since I had an elderly person in the house, I was grateful for him going the extra mile. All around experience was fabulous.
Love the service
Patricia - Vista, CA 92083
We have had Cool Air Solutions maintaining our HVAC system since we bought our home in 2017. They have always been kind and respectful. They also provide details and even pictures to help describe when things are broken or need to be replaced (our furnace is in the attic which we don’t go into). Thanks so much!
Chris - Vista, CA 92083
Jorge Cervantes is just the BEST service provider ever!!! He was courteous, timely, and answered all my numerous questions about the repair needed. I will always use this company and ask for Jorge. You can't go wrong with him!
Furnace visit gone great
Rod - Vista, CA 92083
Good job. Very attentive. Asked for some additional future services and they accommodated. Setup another appointment next week. Just a bit unsatisfied that the putty they keep fixing was not fixed.
Barbara - Vista, CA 92084
Tech did an awesome job! Very knowledgeable and professional! Thank you!
Great Service, Wonderful Customer Support
Chris - Vista, CA 92083
This tech was so outstanding! Very polite, on time, listened to my concerns and addressed each one
Kathleen - Vista, CA 92081
Kendall was personable and spent time explaining everything and answering all my questions.
Lynn - Vista, CA 92084
Very profession and helpful
Nancy - Vista, CA 92084
Great service dept.
Jane - Vista, CA 92081
Jon - Vista, CA 92084
Luis, was very knowledgeable, professional , friendly and was very honest. It's hard to find employees that. I feel like we want to keep using Cool Solutions for our upcoming repairs.
Great service by Patrick and Steven
Elizabeth - Vista, CA 92081
Courteous and professional installation of new ductwork for our air conditioning system. Protected carpet and cleaned up any debris and removed old ductwork.
Tre did a great job
Josh - Vista, CA 92081
Charles - Vista, CA 92084
Great personal service
Kathleen - Vista, CA 92084
As always, CoolAir is wonderful to work with. Kendall was respectful of my home, was very clear with what had been inspected and explained in detail his findings, what I can expect from my system in the next few years and any steps necessary to keep things running smoothly.
Nestle - Vista, CA 92083
Jimmy came on time and explained everything to be done. Assessed thoroughly and found the problem. Went to work and now my AC is back working 100%. ThaNks Jimmy!
Arrived on site to preform maintenance but system was not working properly since the morning. Found 2001 Rheem heater non operational due to failed inducer motor. Indoor blower is leaking oil as well. Flame sensor was rusted. Unit is cover in rat droppings at this time due to rodents. Clients are not in a position to replace due upcoming weddings. Clients wil op for mandatory repair for meanwhile and understand that these repair will not guarantee extra life. Inducer was ordere upon departure. Do not recommend running unit.
Maintenance performed on Goodman system. Checked ampâ€™s of blower motor and furnace itself, system using low amps. The filter was still clean and can be replaced next maintenance visit. The temperature split was in range to heat home properly. Coil is clean, and gas line is in open position. Turned heating off and checked through all electrical components. All components operating correctly. System is operational upon departure. Moved onto Lennox mini split and set in heating mode. Cleaned out air filters inside mini split head. Checked voltage tightened electrical. Noticed the condenser was dirty so I went ahead and cleaned off unit. System heats well, and operational upon departure.
Furnace wasnâ€™t operating upon arrival. I started my diagnostic and found the spark igniter module failing. System couldnâ€™t turn on heat, just fan spinning only. The blower motor is in bad condition and is unbalanced. You can hear the bearings of motor moving while system on. The motor using high amps while running, and system canâ€™t operate how it used to. Looked into Rudd air conditioning equipment and they no longer make nor sell parts from distribution or distributors. System is from 1985, system needs to be replaced. Just charging for diagnostic today, after calling distributors and them verifying systems parts arenâ€™t made anymore due to old age.
Furnace check up on twenty year old system. System wasnâ€™t operation correctly. Owner replaced thermostat himself and couldnâ€™t get system on. I was able to turn on system and after I cleared every error code. System gave me a new one after clearing each one. I found a faulty blower motor, a motor control reading low, pressure switches that didnâ€™t close. I brought all these issues up to owner. He agrees to just replace instead of put money into old system. Only charging for diagnostic today, and supervisor will arrive on Wednesday from 9-11am
Furnace is in bad condition, the whole inside is filled with rat droppings. The sensor was cleaned to get system on, but didnâ€™t work. The thermostat is failing and very old. Thermostat calls for heating minutes later. The system has a lot of parts failing internally but canâ€™t be replaced because parts are exceeding age of parts at distribution. Charging for diagnostic only today. Supervisor will come out from 2-4pm.
Arrived on site to perform heating tune up on a 2017 Goodman unit. Client stated no issues. Cycled unit and is operational. Filter was just replaced. Blower assembly and wheel is good slight dust. Motor is good. Secondary motor control is good l. Inducer motor is in range. Igniter is good. Flame sensor was cleaned. Drain lines a hood and drain pump hood and operation. Found no protection on unit and would recommend adding some to protect unit from electrical surges and power outages. Cycled unit but and went over how unit is running and itâ€™s condition. Went over recommend he is aware and did hold of now. Cycled unit and unit is operational upon departure.
Recovery, vacuum and system recharge.
90% furnace venting was leaking from roof -There was no vent cap on the roof, causing water to get inside and leak into furnace and cabinet -The pvc venting is also not sealed properly as well as the b-vent in the roof -I installed a cap onto venting to ensure no water leaks in -I also sealed the unsealed part of the venting with roof patch and high-temp silicone
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. House heats up to designated temperature. I checked out blower motor of any dirt or debris and itâ€™s clean. Replaced air filter for new air filter. Hot surface igniter not cracked or having white spots. Flame sensor still working good, flame sensor cleaned. Ducting done correctly, and all runs intact. Inducer motor is working high amps along with furnace. House heats good and ready for winter. Fixed duct run that led to living area, duct has better air flow now.
Electrical connections tightened -Amperage for fan motors are within range -Thermostats working properly -Contactors are closing efficiently, although are a little pitted -Constant 240 volts -24v is constant as well
Performed combo tuneup on 2 year old AC PRO unit. Cleaned return grate. Replaced filter with new owner-supplied MERV 16 filter. Inspected blower compartment and found blower wheel to be clean and balanced. Checked all electrical connections. Cleaned flame sensor. Tested resistance of hot surface igniter. Temperature rise and split are within limits. Cleaned heat pump coil fins and inside/outside of unit. Inspected electrical compartment. Prior to departure I ensured the furnace is operating as expected.
Replaced board system is operational.
Upon arrival performed diagnostic, found motor to be running without a call for anything. Disconnected all wires to circuit board & system still runs. Circuit board has very big burnt spots. System is operational just can never stops running. Left unplugged.
Upon arrival performed diagnostic on heating system. Changed out igniter. Flame sensor cleaned. Filter swapped client provided. Circuit board and electricals are good. Blower wheel is clean. UV LIGHT BALLAST IT OUT. System is very clean very efficient. Washed outdoor coil. Checked refrigerant. Circuit boards look good. Compressor amps in range. System is operational.
Technician arrived to perform mini split tune up -Refrigerant levels are within range -Filters cleaned out -Both heating and cooling working properly -Client would like a lineset cover and lineset insulated again -System is currently heating upon departure
Upon arrival preformed a 20 point maintenance, unit was running in heat when I arrived. I started my tests with a temp rise, the temperature rise was a little high and when I tested the induced draw it was high as well. After changing filters and doing some investigating I found 3 vents closed which contributed to the high temp rise and high induce draw. Once vents were all opened and filter was changed, inducer reading was back to normal and so was temp rise. I did recommend dampers to help with air flow distribution throughout the house. Next I checked all burners and assembly and made sure the combustion was properly venting though the flue vent. Next I took a static pressure test which came back good and within range. Ducting was sized properly and air flow was good. Took a reading of all other electrical components and they all came back within the designed range. I did recommend surge protection on his furnace which we did install. Indoor unit is now protected for surges and powe
Performed heating maintenance on 8 year old AC Pro unit.<br> <br> Cleaned return grate. Inspected filter and found it to be in good condition. Flushed condensate drain with water. Temperature rise is within limits. Checked all electrical connections. Tested all safety switches and pressure switch. Cleaned flame sensor. Tested resistance of hot surface igniter. Inspected blower compartment and found blower wheel to be balanced but dirty, it was recommended to Nick that he have it cleaned. No surge protective devices are installed on the furnace, this too was recommended to Nick.<br> <br> Prior to departure I ensured the furnace was operative after my maintenance inspection.
Inspected the ducting and the attic space, reattached bathroom fan vent.
Refrigerant was recovered and recharged to proper specs<br> -8 lbs of refrigerant was added -System is now working properly -Client is also now apart of our comfort club
Mini split check up on a three head unit. I operated all functioning heads to heating mode and rose to highest heat point. I hooked up my gauges and all my pressures were in range. I checked for refrigerant leak and there are no indications that the system in low. Filters were all clean in all three mini split heads. The system ran for hour and a half with no error codes. Owner wanted me to check if installation was done correctly. I made owner aware that these systems go into defrost mode to cool down compressor. That explained his burst of cool air after hours of running. System is operational upon departure.
Mini split was installed multiple years ago, date canâ€™t be located -System was installed cutting some corners -Client is aware it may take a couple visits and repairs to really figure out what is going on -System is reaching 650 psi and cutting out every 5 minutes -Madison is coming out tomorrow to provide replacement options
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. I checked out blower motor of any dirt or debris and itâ€™s clean. Replaced air filter for new air filter. Owner had extra one, so just used his. Hot surface igniter not cracked or having white spots. Flame sensor still working good, no need to be cleaned. Ducting done correctly, and all runs intact. Inducer motor is working high amps. House heats good and ready for winter.
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. Temp rise of 25-55 needed, I got a temp rise of 30. House heats up to designated temperature. I checked out blower motor of any dirt or debris and its clean now. Motor was replaced. Filter still good till next maintenance. Hot surface igniter not cracked or having white spots. Flame sensor still working good, no need to be cleaned. Ducting done correctly, and all runs intact. Inducer motor is using max amps. House heats good and ready for winter. Will call in office when wanting to re new maintenance agreement or services.
Arrived on site to perform heat pump diagnostic on 2022 X series unit. Upon arrival homeowner stated They have recently moved in in the past homeowners replace the unit with another company going fully electric. Now the unit does not heat up the house. Begin troubleshooting at outdoor unit and found error code H4 indicating overload. Contacted technical support and they advised re-wing the refrigerant charge into the unit and pulling a proper vacuum. This would have to be the first step and unfortunately we will have to charge for refrigerant and labor to do the work. Client is aware and will be trying to get in contact with the initial people that installed the unit. Klein will give us a call back if you cannot find the company in upon departure unit is non-operational.
Technician arrived to perform furnace tune up -Flame sensor cleaned off -Filter is still clean until next visit -Heating elements are all working efficiently -Electrical connections tightened -Resistance for motor and igniter is within range -System is in great condition