Are you having trouble keeping your Ramona CA home comfortable? Do you question the quality of your home’s air? Does your home’s energy performance need improvement?
Cool Air Solutions has been solving these problems since 2006 as we repair, replace and maintain the heating and cooling systems of your Ramona CA neighbors. Call us to find out what we can do for you!
for Ramona, CA
Our Reviews by City
Kenneth - Ramona, CA
Came when requested. Very informative.
Great service, reasonably priced, highly recommended
Mira - Ramona, CA
Scheduling and staff were awesome, our technician Jorge was a sweetheart, very honest and very knowledgeable, all in all we ate a very happy customer.
"Great Service, Fair Price!"
Martin - Ramona, CA
Mr. Cervantes was very professional and polite. I especially appreciate that he was knowledgeable and competent concerning the task at hand and explained why and what he was doing. Sincerely.
Arrived on site to perform AC/heating maintenance on 2010 Goodman heatpump.
Upon arrival performed heating tune up. Checked heat exchangers, did not find any that were damaged or cracked. Circuit board and electrical connections in range. Indoor blower motors are leaking oil and need some replacement soon. Client stated they donâ€™t use heater that much due to propane costs. Advised moving to a dual fuel system to utilize solar on home and use propane as back up cause be a good outcome. Indoor blower wheels are dirty. Dusted off electrical connections. Did not have any filters for client. System checked, system operational. Client wanted to email husband with all pictures.
Performed heating and cooling maintenance on a 2020 Lennox heat pump. All electrical components were measured tested and recorded. Refrigerant levels are in range. Filter is ok today. Indoor unit was chemically washed. Outdoor unit was very dirty and chemically washed today. Condition of system was discussed with the homeowner. A maintenance schedule was Setup. System is fully operational.
Adjusted circuit board setting to stage to second stage after 7 minutes of heating. Tested supply temperatures and monitored. Removed piece of gas nipple in the attic space and removed length of return ducting. Programmed the Sensi app and connected the WiFi network. Added a summer and a winter schedule for the thermostat.
Installation of a Lennox Variable Speed Furnace. Cash Discount is only applicable if payment is completed with either Cash or Check, failure to do so with result in cash discount being revoked.
Upon arrival found system not heating. Blower motor would stay on for 30 mins plus after call for heating ended. Upon inspection found the control module yellow and had failed. Further inspection revealed the ignition components are old and worn down. Blower motor is leaking oil. Tried to replace with universal board on van but it wasnâ€™t the correct one. Order control module. Client is interested for replacement of furnace since part is a couple days out.
Tech arrived on site. Performed fall tune up. Inspected ignition components. Unit is 21 years old. Flame sensor is oxidized, and hot surface igniter has high readings. Both still operational. Inducer motor is okay. Blower motor is over amping and will fail. Pulled blower motor to inspect heat exchanger. Temp rise and static are okay. Heat exchanger is not cracked at this time. Hot spots on heat exchanger. No secondary drain pan on condensate line. Talked about replacement options as well as repair options. Unit is operational upon departure.
Combo Maintenance Performed Upon arrival system is working and operational. I began my maintenance in the attic by performing a duct leakage inspection. I then proceeded to the furnace unit, I checked and tightened electrical connections. I inspected the heating components for proper operation and wear. Burners were inspected for proper operation. Flame sensor was cleaned. Condensates lines were inspected for proper drainage. Static pressures and temperature splits were taken. Filter has been checked, does not need to be changed at this time. Blower housing and wheel was inspected for balance and dust build up. Air supply was measured. Inspected safety switches as well as inspected home for fire and carbon monoxide detectors. I then proceeded to the outdoor unit. I checked electrical components as well as measured amp draws. Inspected components for wear. Checked refrigerant pressures. Recommended a phenomenal aire to customer for allergies and dust concern. Upon departure system is w
Customer was confused on todayâ€™s scheduling, he thought todayâ€™s visit was being rescheduled. He is leaving in 35 minutes. No time for a combo tuneup and is happy to reschedule. Customer is nice, states if there is any bill for the mixup to go ahead and email it.
Upon arrival performed diagnostic. Client saidnsystem just keeps running and running after doing its cycle. Client had some registers closed, dirty filter. Advised we have to keep filters clean every 2 months. System is operating at normal standard, reaches out of temperature, cycle to cool heat exchanger down then shuts off. System is operational. Client will speak to husband about membership.
Found defective condensate float switches keeping the system from operating properly.
Tech arrived on site. Started AC tune up on a Rheem split system. Unit is operational. Cleaned condenser coils with chemicals. Cleaned and tested components in the electrical cabinet. All start components are good and had been replaced recently. Condenser fan motor is leaking oil and rusty. It is recommended that it be replaced before it fails. Refrigerant charge and temperature split are good. Went into attic and started checking Airflow. Static pressure is low. Duct connections are not sealed. Blower wheel is dirty, and there is no emergency drain pan installed. Flushed out condensate line. It is strongly recommended that we install an emergency drain pan to prevent ceiling damage in the event that both lines clog up. Compressor amps are 18/21. Compressor is struggling. Service disconnect is not secure on the wall. Went over replacement options with client. Customer is aware of all issues and recommendations. Client declined them at this time. Unit is operational upon d
Inspected duct system and performed assessment of the entire homes temperature splits and layout.
Tested system for operation. Measured temperatures. Added refrigerant charge. Inspected air filter. Tested welds for leaks with soap bubbles. Inspected fan motor and evaporator. Inspected attic space and ducting. Tested temperature splits at the return grille, and at the system.
Installation of a Lennox 16 SEER Single Stage A/C with High Performance Coil Add on inducing lineset, electrical 220/208V was ran by homeowner in the previous years. Pricing shown will be check pricing including every applicable discount
Arrived on site to perform AC maintenance on 17 year old Goodman systems. As homeowner was showing me around, she mentioned that they recently were in the market to replace the system and had gotten a couple different quotes. After realizing how much an expense like that would be, they are no longer looking to replace the systems as they are most likely going to be selling the home and moving. They are hoping that a maintenance will hopefully make systems run smoother and squeeze some life out of them. Advised I will be doing thorough maintenance and inspection and will let them know how them systems are doing. Cycled systems for cooling. Checked outdoor units electrical and system components. Primary motor controls for main unit has burn and pit marks. Secondary motor controls are in range. Amp draws for compressor and condenser fan motor are within range. Condenser fan motors are both leaking oil. Compressors are starting up hard, and they are noisy. Refrigerant levels are within ran
Replace existing system with listed equipment. Shift furnace over and open space for water regulator. Hard pipe return duct.
Inspected system for faults and tested components
Performed combo tune up on 20 year old Rheem system. Cycled system through heating and cooling modes. Checked indoor unit electrical and system components. Blower wheel was completely dirty. Blower wheel had sucked up the plastics from the wiring diagram as well as the flashing codes and were making a ticking noise. Indoor blower motor has lost a significant amount of oil and is pulling quite a bit of energy. Pulled blower wheel off and opened up coil compartment to inspect heat exchanger. Heat exchanger has a lot of hot spots throughout each chamber as well as the collectors box. Temperature rise across heat exchanger is slightly high but still within range. Checked outdoor unit electrical and system components. Several components were recently replaced and they are all within range and operating properly. Compressor Amperage is high and is really close to going over allowed maximum capacity. Condenser fan motor has not been replaced and it is also pulling in more power than what it
Upon arrival performed maintenance. Outdoor noise was taken care of for client. System does not rattle anymore. Washed outdoor condenser coils and caging on system. Set up refrigerant gauges for pressure, found system, to be with the perfect range for refrigerant levels. 20 degree split. Advised client air scrubber would definitely help dust inside of home. Will follow up. System is in very good condtion. System was reset tested and fully functional upon departure.
Ran callback. Customer said system is still tripping the breaker when he runs it. Replaced breaker, disassembled the condensing unit sprayed chemicals inside and out to completely wash it and remove any buildup on the condenser making it work harder. Let the system run for 35-45 minutes uninterrupted. Turned the thermostat off, tried to recreate the situation, turned thermostat back on while system is warm. System turned on fine, no tripped breaker. Tried single stage, and second stage. No issues. Cycled system off and on. System is operational upon departure. If issue does occur again will request a senior tech or Lennox rep to come out and re-check findings. Per Andrew to install a compressor saver kit.
Arrived to home. Customer said system has been blowing room temperature air. He cycled the system on and was, Showed me around and we noticed condensing unit wasnâ€™t operating. Opened up the condensing unit primary motor control was engaged getting 24v from the thermostat, checked power coming in and was getting 8v. Not the 240 needed to power the system on, same at the disconnect. Checked breaker and was tripped. Customer said they got a power outage two weeks ago, have not cycled the system on since then. Says they get power outages regularly. Approved recommendation to install surge protection for both indoor and outdoor systems. And also for our membership plan. Received his 20% on repairs or upgrades. Hooked up gauges to check pressures and are within limit, checked compressor run amps and is within range. Cycled system off and on. System is operational upon departure.
Arrived on site to diagnose 2 20 year old leaking system. Client is moving in upon moving in he noticed house had had condensate leak issues in past as he dose already have water damage in master bed room. Client he is in the process of moving and is in escrow so wanted to ensure leaking isssue was fixed. Did indoor unit inspection. Found drain lines not drain and dirty. Once it got to p-trapsit did not drain properly bathroom sink. Advised client of issues. Took drain lines off under bath room sink and saw there is build up clogging up drain lines. went over repair and replacement options. Client dose want to hold off on replacement until next year but did want to go forward with clearing out drain lines! Replacing p-traps, cleaning evaporator coils, and joining our maintenance plan. Vacuumed, blew out, pressure tested, and cleaned drain lines and tested drain lines to ensure itâ€™s now draining properly. Had client with me to visually see itâ€™s go cleared and draining now as I tes
Arrived on site to trouble shoot system. Homeowner stated that his furnace is not turning on and he cycled on his AC and that didnâ€™t kick on either. Thermostat is showing that system is heating but system is unresponsive. Found error code E-111 on furnace board stating that system polarity is reversed. After speaking to homeowner, he had an electrician out the day before. System did stop operating shortly after. Unfortunately there would be a charge to repair wiring, unless homeowner calls his electrician back out to fix. He gave me the ok to repair. Re-wired furnace high voltage. Kicked power back on. System fired right up and started heating, no more error code on board. Cycled AC as well everything is working perfectly now. System is fully operational upon departure.