Heating, AC & Indoor Air Quality
Cool Air Solutions has provided Poway CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your Poway CA call us first when they need help making or keeping thier home comfortable.
for Poway, CA
Our Reviews by City
Cheryl - Poway, CA
On time polite. Let me know that cool solutions works around permitting by having the homeowner do it. dont know yet if I should worry
Steve - Poway, CA
Michael was terrific. Professional, courteous and knowledgeable. Another great experience with Cool Air Solutions who I have been doing business with for 5 years.
Dave - Poway, CA
Excellent service and installation! Great job!
Very Happy with Bid
Bill - Poway, CA
Brian spent much time examining my present system and discussing the various options for its replacement.
Installation of 2 Ton XC20 Variable Speed 20 SEER Gold Package, including electrical and line-set. Total will be paid in check upon completion.
Replacing downflow evaporator coil and adding R410a
Performed AC diagnostic on Goodman condensing unit. Upon diagnostic found that dual run capacitor on hermetic side terminal no longer holding microfarads. Upon replacing capacitor ran system for 10 minutes and measured R-410A refrigerant pressures to conclude that TXV thermal expansion valve contains a restriction on the liquid line causing sub cooling to be high and superheat. This is causing capillary tubes to ice up and evaporator coil. Head pressure is above 400 psi and low psi is 90. Thermal expansion valve needs to be replaced and ordered with a return visit. Customer is aware of that and will be contacted in the morning. This will include in a Adjustable charge of 2 pounds of R410A
Casita = Replace existing system with new Lennox 2-ton split system 2-stage. Fabricate rectangular 28x10 return system on right side of furnace closet to attic. Install 14â€ flex duct to high wall return cut-in for the casita. Re-locate thermostat to service casita. Save Exiting 2-stage American Standard Furnace and Purification for Main house. Main House = Install American Standard furnace + Lennox Silver cooling only package. Provide return platform in closet conversion, include return air system, provide all gas, electrical, refrigerant lines, and Exhaust systems per code. Provide and design full r-6 class 1 duct system with 7 total new supplies thru out the home. Kitchen and 1- Living room vent will have exposed metal ducts running thru the bathroom and office (customer to decide on soffit or paint) All Permits and HERS testing included. $25,367 Due upon completion. After Lennox rebate total $24,942 Remove Both existing wall heaters (patch not included) Exclusions to pric
SDGE inventory and assessment in Poway on some Goodman systems.
Performed routine fall maintenance on 2 lennox furnaces
Air conditioner diagnostic
Two system air conditioning maintenance in Poway.
Two system air conditioning service in Indian Trail Estates.
Adding air conditioning to a heat only home in Poway and upgrading filtration system and blower motor
Helping a customer on changing a complete heating and air system