Heating, AC & Indoor Air Quality
Cool Air Solutions has provided San Marcos CA air conditioning and heating solutions since 2006. Our services include installation, design, repair and maintenance for residential and commercial clients.
Read our reviews below to learn why your San Marcos CA call us first when they need help making or keeping thier home comfortable.
for San Marcos, CA
Our Reviews by City
Amy - San Marcos, CA
Great crew! from sales to install to service
Rick - San Marcos, CA
I found your staff for sales install and service to be thorough, conscientious, and professional, the installers did a nice clean installation.
Leuella - San Marcos, CA
He was very nice friendly efficient knowledgeable I had no problem whatsoever with him
Leuella - San Marcos, CA
Very well very informative very kind
Quick service all good
Alice - San Marcos, CA
Luis found the problem, fixed it!
Lorna - San Marcos, CA
Armando - San Marcos, CA
Very Happy With The Service Of The Service Personal
Efficient & Timely Service
Richard - San Marcos, CA
Luke arrived an hour early! Of course he called to confirm we would be home... Service was friendly, efficient and he had the parts to make the repair on our home AC unit in 30 min. We are once again sitting in cool comfort.
6 month checkup
J.Hawks - San Marcos, CA
Got a call to set up the appointment and Luke came out on time. He was friendly and professional and really cared about my satisfaction. Everything is fine.
Mary - San Marcos, CA
MICHAEL PIERSON DID A GREAT JOB IN SERVICING MY A/C. HE IS HONEST, PROFESSIONAL, POLITE AND PROMPT. I HIGHLY RECOMMEND "COOL AIR SOULUTIONS" FOR YOUR HVAC NEEDS.
Great service, quick diagnostic, and Adam had my system running in 20 minutes.
Charles - San Marcos, CA
Very knowledgable Technician, and was able to explain things in a way I could understand.
Great and knowledgeable service.
Cindy - San Marcos, CA
Everything was explained in easy to understand language.
Great Service using Cool Air Solutions
Mary - San Marcos, CA
I have been getting great service from Cool Air Solutions since 2011. I actually met them at a job site that I was working at with my cousin who is an electrical contractor in Temecula/Del Luz. We were wiring a brand new house and Cool Air Solution was installing all the heating and air equipment. I was impressed with there professionalism and knowledge so I asked them if they would maintain my new air conditioner and new furnace that I bought a couple years prior and have been a satisfied customer ever since. They come out twice a year to make sure my systems are working properly or whatever needs to be done. Today Luke was my service tech and he was courteous, professional and explained what he was going to do. Also, they always call me to let me know they are on there way. Great company and I am just appreciative that they drive all the way to San Marcos. Thank you again. Mary Aiello-Melfi
Great informative quote
Jacqueline - San Marcos, CA
Brian Carr and Bob Marson (Lowe's) were a delight to deal with. They were punctual, listened to our concerns and requests and went over all of the options thoroughly. At no time did we feel rushed or pressured.
Tina - San Marcos, CA
Luis - San Marcos, CA
Brian was really good explaining all the new technology and what would it do to save energy.
Bryan - San Marcos, CA
Just had a quote from these guys. From the Mary who answered the phone to Brian who gave me the quote. Both really seem to understand customer service
Upon arrival performed diagnostic. Customer believes thermostat runs without being called. Temperature at thermostat is same temperature it displays, ran a test to see if system dropped down to temperature. Thermostat is right over return. Thermostat and area are correct temperature. Customer,we just wanted verification. System operational.
Found system operational upon arrival. Customer said thermostat gave out error code â€œcriticalâ€™. Checked system and found no saved error codes. Checked electrical and freon pressures. Everything was within range. Customer said unit only had that error code once and then it went away. No repairs done today. Unit operational upon departure. 1. Recommend adding extended warranty to cover labor, freon, and warranty processing. 2. Recommend surge protection for air conditioner. Customer declined recommendations today.
Found system operational upon arrival. Customer stated she had electrician neighbor come out and diagnose and work on system. She stated the outdoor fan wasnâ€™t running and electrician checked all the electrical and cleaned the drain line in the attic. Upon inspection, found compressor and condenser motor running. Unit was low on freon. Customer approved adding freon and leak seal. If leak seal doesnâ€™t seal leak this turns into a leak search which will help us pinpoint the leak and determine action required to repair leak. Added refrigerant and sealant. Unit cooling to a 12 sub cool and 12-15 superheat upon departure. ***Customer also signed up for monthly maintenance agreement. This included a discount on repairs and a waived diagnostic as part of the membership benefits. If maintenance agreement is canceled, discounted rates are also canceled and due.***
Upon arrival performed diagnostic. System is very low on charge. Outdoor coils are very damaged. Indoor fan motor leaking excessive oil. System is R-22. Duct work is very old and has old distributor boxes. System is operational but not cooling efficiently due to low charge. Darren to come out Tuesday between 2-4.
Customer paying check upon completion
Replace existing system with listed equipment. Permits and HERS included
Performed diagnostic on 2003 Payne unit. Homeowner states system is not blowing any air at all inside the home. Cycled system for cooling. Outdoor unit kicks on, indoor unit is unresponsive. Checked system electrical and system components. System is recieving proper voltage. Thermostat is sending proper command to circuit board but indoor fan is not turning on. Secondary motor control for indoor fan still in range. After testing, found that circuit board is not sending power for the fan to kick on. Circuit board needs to be replaced. Tested fan motor separately with pig tail and motor kicks on so motor appears to still be good. Can not perform thorough evaluation of system until circuit board is replaced. Went over findings and recommendations with homeowner. She wants to call her home warranty and see if there is anything that can be done or if they can give her any money for the repairs. System was left non operational upon departure.
Tested both systems and measured indoor temperatures. Replaced filters. Checked outdoor electrical and measured voltages and amps. Leaned condenser coils. Verified refrigerant charge.
Heating and cooling tune up
Install Lennox 16 SEER single speed complete system. Install 5â€ Media filter kit. Relocate and enlarge supply register in living room to 12x12 (customer to take care of patch work). Add new supply register to master bathroom. Seal all cans and install high flow bar style registers. Build catwalk, light and switch, extend gas and electrical add ceiling return air. Permits and HERS testing included.
We will be installing a new Bryant slim line condenser only. This includes a condenser pad with service disconnect. Also includes permits and everything included in the permit process
Performed system operations tune up and maintenance on both heating and cooling systems. Checked all electrical components and controls. Measured airflow and recorded temperatures. Cleaned outdoor coil and indoor blower cabinet. Changed air filter. Cleaned flame sensor and condensate drain.
Upon arrival performed condensate drain box. And brand new venting proper venting
Pressure switch hose was open. System now functional
Upon arrival performed maintenance. Collectors box is cracked & needs to be replaced. Venting is completely wrong needs pvc ran. Have power shut off due to leaking water and could cause damage to system. Coming back out to replace parts. Collected 216, 1945 due upon completion.
Ac check up
Performed performance check and cleaning of the furnace. Checked electrical. Components and temperature rise. Checked heat exchanger for reliability and monitored operation of the heater.
Thermostat replacement in San Marcos, Ca.
Furnace maintenance in San Marcos, Ca.