Cool Air Solutions has provided Santa Ana CA air conditioning and heating solutions since 2006. Our services include installation, repair, maintenance and more for residential and commercial clients.
Read our reviews to see why your Santa Ana CA neighbors call us first when they need help making or keeping their home comfortable.
for Santa Ana, CA
Our Reviews by City
Joe - Santa Ana, CA
Appreciate the attention to detail and kindness of everyone on the team.
Don - Santa Ana, CA
Tyler was outstanding. Thorough, courteous, knowledgable
Very high quality maintenance. Honest and reasonable.
Thomas - Santa Ana, CA
Great service. Tech showed up on time. Clear and efficient dispatcher. Worked efficiently and professionally, covered shoes, immaculate, fixed HVAC filter mount issue - no charge, honest evaluation of heating and AC systems. Offered recommendations. No upcharges. Good attitude.
Arrived on site and performed combo tune up on system. Tested heat and checked for safety issues. All checked out filter is restricted and should be replaced. Advised client to get them online. Cleaned condenser coil and whiled down system with uv protective coating. Cleaned off electrical terminals. Refrigerant charge and temp split are good. System is operational upon departure. Found newly installed Samsung mini split low on charge. Inspection found leak is most likely near head unit. Lineset cover is not installed the best. Placement of unit could be more centered for better efficiency. Client is having installing company come out to warranty work.
Post job walk
Installed heat strips, tested equipment and programmed control.
This system qualifies for 3 promotional financing offers: 3 months no interest no payments into a reduced 6.99% apr at 233 a month or 18 months no interest with payment or 12 months no interest no payments Total job would be 23059 after all rebates and incentives. $3000 of this project will be paid by cal tech California. 20059 could be paid by cash, check, cc or special financing shown above
Collected a deposit of 3391 by check #107. Balance due paid with financing for 25000.
Performed furnace and AC diagnostic on 2003 system. Upon my diagnostic I found that the AC was operational although had a weak capacitor. And then proceeded on my furnace diagnostic and found out he secondary motor control for the fan had gone out due to the fan over amping. Further investigation show that pulling the blower wheel from the compartment I found that the motor had leaked oil and was covered in debris. Recommended blower wheel cleaning and motor replacement. System is fully operational upon departure heating and cooling and customer has signed up with maintenance plan for two times a year
Doing a single system air conditioner and heater maintenance out here in North Tustin
Aiemr conditioning service in Santa Ana