Cool Air Solutions has provided Spring Valley CA air conditioning and heating solutions since 2006. Our services include installation, repair, maintenance and more for residential and commercial clients.
Read our reviews to see why your Spring Valley CA neighbors call us first when they need help making or keeping their home comfortable.
for Spring Valley, CA
Our Reviews by City
Sarah - Spring Valley, CA
Nate and Patrick were efficient, polite and prompt. We would definitely recommend Cool Air Solutions based on their work.
Very good service
Maria - Spring Valley, CA
Jimmy was great. Very knowledgeable and friendly.
Excellent job. Very professional.
Rena - Spring Valley, CA
The technician took extensive time to check the whole system, including the A/C unit, explaining what needs to be done in the future.
Mark - Spring Valley, CA
Arrived on site and performed AC maintenance on 2016 Lenox unit
Upon arrival performed Maintenance on heating system. Found filter to be dirty, client buys his own online. Recommended adding surge protection to keep circuit boards and electrical protected. Signed client up with maintenance plan. Cleaned flame sensors. Temp splits in range. Static pressures good. Dusted off all electrical components. Ducting in great condition. Thermostat in working order. Amperages are in range. System is operational upon departure.
Performed routine spring maintenance on Lennox condenser in Spring Valley. Tessa verify correct operation of system, recommend staying on maintenance plan due to the condenser being extremely dirty at time of visit. This is the first of two visits with the maintenance plan they will be up for renewal on the next visit. Clean entire outdoor unit back to factory fresh, system is running correctly at this time.
Replaced thermostat with NestPro and set up homeowner WiFi network
Upon arrival found thermostat to be faulty. Does not engage for heating, replaced under warranty and installed a honey well T6 pro WiFi, replaced filter. System is operational upon departure.
Arrived on site to diagnose a air flow issues on a 2019 good and system. 2019 Condenser in back yard. 2000 furnace and 2019 evaporator coil located in garage. Spoke to client about issue a a she stated she feel system is not producing enough air flow to master and would like to see what can be done to provide more air flow to master bed room. As well there is a noise being made when ever blower is operating. Found due to age of system and itâ€™s condition blower assembly now has some play on assembly as it has creates a bit of vibration When operating. She cycled system on cooling. Both units operating. Inspect attic and duct. All good. Inspected furnace. Found filter dirty and in need of replacing. Recommend doing more frequently to reduce the amount of dirt entering system. found blower motor has been leaking oil in past as dirt and oil are building up. Blower wheel is heavily dirt from lack of filter change out. Creating high stress on blower motor and making it work harder due to
Replace existing system with listed equipment. Seal return platform, install new Merv 11 5â€ filtration system, install new condensate pump under platform, seal and install new high flow register set and seal cans. permits and HERS included
Performed AC maintenance
Also includes Merv 16 filter promo on both units
A.c. maintenance in Spring Valley
Sdge quality maintenance on Weather King equipment
Furnace maintenance and filter replacement in Spring Valley