Our team's mission is to improve the lives of our clients by providing the most reliable, efficient and comfortable environment in the home and workplace. All with old school manners, work-ethic and customer service!
Name: David R
Replace E30 display under warranty
Adapt new cooling system to existing 6 year old Lennox Furnace.
Outdoor unit making high pitched electronic sound do to the inverter and outdoor fan motor.
18 mo no interest financing available
system not cooling. Condenser not coming on.
Attic fan would not shut off.
Re-positioned secondary pan under the air handler. reconfigured the condensation drain line to allow for proper drainage. leveled the air handler under the home. cleaned up all trash and debris under the home. Checked the refrigerant charge and tested the system for proper operation.
Condenser starting component is weak and in need of replacement.
Polarity reversed on line voltage wire.
Found that the unit was not leveled properly causing the coil to drain on the inside insulation of the unit.
This is the best and long term solution for the price.
Replaced TXV under warranty and performed spring/summer maintenance
Air flow adjustment to front 2 rooms.
S30 thermostat frozen
Arrived to find that the system was not closing off airflow between floors properly. Found that no only are ducts attached to the wrong zones but the proportional zoning system is unable to close off airflow properly.
Air flow to the second floor is not proportionally controlled by the zoning system. The system uses a blade damper that directs the airflow but does not limit it. This was used by the builder to eliminate the need for a barometric relief or 2 stage equipment. The down side is it does not allow one floor to be controlled truly independent of another.
This includes a complete system replacement and removal and disposal of the old equipment.
System not cooling as well as it could
Ac breaker in off position
Manufacturer forgot to drill primary drain hole in drain pan.
Repair damaged line voltage wire that shorted.
Replace furnace with new Lennox furnace, increase exhaust vent size to 4â€ adapt to and seal all ducting. Replace thermostat. Includes permits/HERS testing. Patch Attic Access. Convert Furnace to Propane.
Installed ring smart home kit
Cleared error code 224